Type: Posts; User: climate01
...still hear the wind.:whistle:
Does it still work properly in cooling? Superheat ? Sub cool?
What was supply temp?
Wonder what the connection on the drain pan (if there is one) looks like...
I will post some soon.
Would like others opinion on a system where someone piped split Trane 2tta0060a3000aa/4113kp23f to one of the evaporator circuits in a Rheem rtu rrgf131076ckr. 7 lbs 7oz r22 is capacity of Trane...
Take ll temp along path. Visually see how much of coil is boiling off gas. Those two things tell you a lot. Good luck.
How much sub cooling? Indoor temp? How long is unit operating between adjustments? Amp draw on compressor? Did you have 20 delta t when you installed it originally?
Anyone have service/schematics/troubleshooting literature for carrier product# FX4DNF025T00AAAA serial# 4410a68821. Has Honeywell interface module. Fan wouldn't run from vision pro or jumped at...
Trickle nitrogen while you braze. Protect o-rings, txv. Purge air out of hose before charging.
Motivation moves the nation
Thanks for the reply BaldLoonie.
Anyone have documents that specify how to break down rheem/ruud model numbers for gas furnaces, air handlers and coils? (without having a specific model number in question)
Do you have needed voltage? Work your way from fan thru circuit. What was initial problem? Is breaker tripping on immediate startup? Need more info.
x2... always check under load on pm's
I add a suction dryer with compressor changeouts along with performing an acid/moisture test . For general reasons like a leak repair, l install a liquid dryer only. Follow up after system has been...
Two compressors with same starting problem would lead me to check electrical side, after verifying correct charge was added to system. How long does it run before stopping?
Well all i know is i was taught if your brazing nitrogen must be flowing through the lineset. Once you rough in pipes flow travels path of less resistance so the nitrogen will flow at correct psi....
Depends on budget. There are alot of combinations. I try and replace what i use with two. Also keep singles in case i have to join two for certain applications. I hate to have a deep stock of...
There is always the possibility that you started as a tech. After a couple of years you became a contractor which means you are the installer, tech, salesman, etc. untill you hire. A well rounded...
Sarcasm or serious? Either way it wasn't funny to me.
Same principles apply.