Type: Posts; User: francosair
Right on the nail. !!!
It's against the code, run an independent line.
Electric, Heat Pump.
Try with an FF AHU from carrier and return stamp grills at the door, post pics,if you can.
could you please send one to me my e-mail is: email@example.com
thanks on advance.
YOU CAN HAVE THE PART AND A GOOD SERVICE BY CALLING A CONTRACTOR.
CARRIER SALES ONLY TO THEM.
this is the right thing to do.
NOOOOOOOOOO, also silver tape and mastic.
call them back, and have them do it right.
proud regular member,but also a state certified a/c contractor class A, 20 years on the field doing commercial,industrial and residential.so not all the pros are professional members.
Small paint brush and a vacuum
I agree,and is the return opening big enough for your tonnage?
ASK THE TECH TO TEST THE CAP.
one or two breakers for the 20KW?
Ask your friends for any company they used, and referrals
BINGO! I found your problem..............your tech.
I agree old info
It would be best, to have an a/c company install a safety flow switch on that opening. this would stop the unit, if the primary drain blocks.
But first you have to find why it's leaking for that...
If is water leaking, the secondary plug was removed,and because this is a new unit(leaking from the begining) chances are unit was not installed/leveled correctly.
Bad installation,call a real HVAC company they will fix your problem.
water leaks can cause a lot of $$$$$ on damages.
DO NOT EVEN THINK ABOUT CALLING YOUR FRIEND.
Instructions are on all lennox units, just try to find it.
Close all your doors and do not allow that guy in your house.
get a real HVAC PRO.
Right On The Point ! LOL !
It Would Be Cheap to call an air Conditioning company for service.