Type: Posts; User: Paradigm Rob
This job was a real head-scratcher- Happy with how it worked out :)
Has anyone heard of Econoheat and their Omni unit heaters?
How are these used oil burners for installation and maintenance? Any information would be a huge help.
Maybe its not a hole in the heat exchanger?
I had a Lennox G26 with the same issues about a month ago, but it was also melting the intake pipe!
I ended up pulling off the combustion blower and...
I understand from my Trane service rep that this is an issue with most of the TUX and TUH series units. It has to do with too much resistance from the secondary heat exchanger. The engineers got too...
Anyone else out there having a lot of issues with the Trane XR95's (TUH1) pressure switches?
We've had about 70% failure rate, and have been told simply to change out for a high altitude pressure...
Don't even want to think about how to get that triangular duct assembled and installed inside the web trusses... Go with round: much easier on the installer.
Not sure on code issues and/or rebates in Ontario, but in Alberta, we no longer have the option of 80%. You could also be eligible for a rebate on the VS motor, due to electrical savings.
I'd recommend changing it to 3 cycles per hour if it's a high efficiency furnace (plastic venting). Or 5 cycles per hour for a mid.
This will result in longer cycles, which make your system more...
Hate noises under warranty! Toughest to find and fix.
Get your installers to also check the dampers for weatherstripping. I always add it to seal around the damper housing (especially square). Or...
I agree with Roadhouse: sounds like an issue with too much heat/not enough airflow.
May be a limit switch setting (if its adjustable) or duct sizing issue.