Type: Posts; User: OStaine
Try running it using internet explorer instead of firefox.
Had a fan motor making noise. I found the inner race of the ball bearing turning on the shaft. That's because the bearing should have been a press fit instead of a clearance fit. That's just poor...
I've had some training and read some articles on this subject. There are strict guidelines concerning the application of hydrocarbon in supermarkets and there are strict guidelines to remove all...
Any one heard of "redtek"? Its the HC (R12a) replacement for R134a . "Redtek" is not acetylene but its a hydrocarbon and it will fuel a fire. I wonder would happen if a vehicle charge with "redtek"...
Thanks for the Info. I found a Baker Dis.shop in Doral FL., A manager by the name of Tony Peres. He had one so I arranged to have him fedex the oil level control to us, this is for the 10 hp...
Thanks for confirming that. I will replace it.Have a great day , to day ! special thanks to tripointIO and jpsmith1cm :grin2:
sporlan valve OL-60XL; I got oil flowing up to inlet screen of control but not oil is filling crankcase. I check inlet screen but it not plug up . oil pressure in supply line to control is 40 psi....
have a great day FCS.
She is pretty.
Can she take the top off and just cover with a manifold gauge ?
Ok, I will send you one with the proper instructions but please allow some time as this will be costing me.
Please dont order as yet from Smith Enviromentals as this info has not been released to...
Send someone on a plane with test gear and a camara, and I will let you test whatever you want.
Are you ordering one? cause these now come with the correct instructions.
The installation instruction were wrong!
Supply temperature : average 50.3F , Max 50 F, Min 48F
Velocity : Average 852 ft/m , Min 826 , max 895
Return Temp : 77.5 F
TD :27.2 F
Supply Temperature : Average 48.7 F , Max 49.2 , Min 48.2 ...
you are right. You cannot plot the SEER on a PH chart.
You can however, plot a refrigeration cycle on one.
my power quality meter is broken but the Engineer at the electric company will take...
Thanks for being objective.
These are the results I am getting.
I will take some pics.
If you need more info, just ask.
Pressure entaphly Chart
The refrigeration cycle can be plotted on this chart.
Knowing the following:
Hi side pressure, low side pressure, Temperature of refrigerant entering evap(Before...
It looks a little different from that one.
I send a pic later.
The problem with these devices was that the installation instructions were wrong.
I have made the changes and have been getting the type of reading I sent you.
If the units are installed other wise...
condenser Goodman Model# CAL60-1L
evap Pioneer UG060DKA2LA
mechnical device: artic master
This unit has 14 lb R22. and it has been running for two years.
Please note the readings were taken at the same time and the TD varies between 28F and 32F.
This is one of 10 unit running. I know...
Discharge temperature out compressor 157.1F
Suction line temp at compressor 64 F
Air into condenser 84.3 F
Air out condenser 96.9 F
Air into evap 74.6 F
Air out evap 42.9 F
I have install a mechanical device on a 5 ton a/c unit and i got the following results.
Hi side 190 psi, low side 45 and am getting a 30F TD between supply and return. The fan is on high and the...