Type: Posts; User: santhu_hardware
Search: Search took 0.01 seconds.
05-20-2011, 03:13 PM
who not able to solve the problem they definitely blames the product.
As of me it will work. I am also using windows7
Unfortunately costumer losses metasyssysagent (Admin user) password. I tried to reset password with sql tables but not succeed. Is there any otherway to reset password.
THANKS IN ADVANCE]
09-14-2009, 03:55 PM
FX15 controller connected to NAE.its working fine, but when iam going to map BO point to activeX switch controller that is not working. I think some problem with override command for that ...
ok freddy. Thank you for your replay.
What do you mean freddy.......
NAE4.1 and M5 workstation 5.4
there is problem with command(m-inspector). it taking 5 min. to give a command..any body have solution...pls help..
Thanks in advance
12-19-2008, 03:02 AM
Actually when i look into calibration all field are empty(No data).other dx controller working normal with same.....
Iam using dx 9100.In that one AI point showing wrong reading.that is connected to temperature sensor. it showing +8 C degrees differance. howcan i correct this?pls help me.
12-18-2008, 03:34 AM
it doesn't work.I tried with your instructions. in calibration table AO HI value is 10v. i disconnected field and checked with 100% but voltage is same 3v.
12-12-2008, 11:02 AM
Thank you for your replay, Mandamarri is one of the village in Andhrapradesh(India). First i will go with your instructions, then i will give replay.
12-11-2008, 11:21 AM
Iam facing problem with DX9100 AO1 point. at 100% out volatge not exceeds 3v. i checked with jumpers and programming withgx9100 no use. any body can help me on this........
Results 1 to 14 of 14