Type: Posts; User: bar7
r-12 rules hit the nail on the head, with mp-66... the way to go here
you'd think a gas like NU-22 would take over before R410 becomes popular in refrigeration???
call your service tech to fix it
go to a plumbing supply store give them all the specs.. Wirsbro offers a load calc & prices out the job with all the material needed.. Great program to get your hands on for radiant heat
you people who r trying to get free service calls answered or fixed stop being so damn cheap & get your ac fixed
is this a joke???
i got a customer who wants an extemely quiet condensing unit i'm leaning towards a Maytag. Anyone have any real quiet good suggestions?
anybody can assemble a box together... the rest of the install let a field tech take it from there.. EVEN THE WIRING
looking for odd sizes
post any links
any of you people either work on maytag ac systems, or sell their equipment? other than a good warranty & that some of their units come in stainless steel finish, don't know enough... any feedback?
im not gonna lie.. i overreacted with the time clock!!
the guy before me had it set for 35 & 15...r22..no no so i reset it...
the box is self contained.. like i said i was right in the diagnosis of the bad txv...it's just another problem is showing...
robertusa is correct with his statement about humidification in this area...this is a problem sometimes..
but running hot water pipes to an attic airhandler isn't... so i would still recommmend the...
boiler with 2 hydro systems serving 1st & 2nd floors
boiler weil mclein
hydro air air handlers FirstCO,coils
dont know if you have gas or oil for the heating side
remember the airhandler does...
friends always keep us busy huh?
r-22 salad box 2 coils txv
originally customer shows me an ice up coil. i immedatly sell him a time clock... after installing the time clock i check the refrigeration side to find the left side txv...
looking for a link to find a wiring diagram to a 2 door Hussman freezer mn/Gel-2
i'd greatly appreciate it thanks