Type: Posts; User: olsons arctic air
Look at suction line no use running correct size copper either
I bet if you turn off all those fans electric bill will go down
Had a Bryant last summer installed two days later cond. fan blade came off hit compressor discharge line broke and bent fan blade Had to fix copper recharge and replace fan blade Local carrier rep...
Has any one seen any issues with 3.5 ton ( PA3ZN042000)Payne pkg A/C compressors not starting I have three in the last 4 months compressor not starting two were at install one after running about...
thats right the neutral is not just a ground wire it is a load carying conductor if you wire a 110 outlet like that you could overload the neutral wire
Where are you you located I dont know of any code that allows you to drain air handler to sewer stack Install was done against code
got give him credit even put a ground a 3 prong plug on heater