Type: Posts; User: pete_d
Please kindly email me your contact info.
Could you please email me too?
mtnwrench, How much does it cost you for this software?
Please help me.
I want the wiring diagram and spare part list manual of Carrier (France) 30HG 320 901--EE.
Its nameplate is attached.
Thank you in advance
Please help me for 19XR CVC Software CESR-131158-04.
Thank you in advance.
I want these manuals:-
CGAE-IN-3 Cold Generators Air-Cooled
CGAE-M-3 Air Cooled Cold Generators
CGAE-W-2 Wiring Manual
Please kindly email me. My email is in my...
You can replace the dynaview (with correct MP software) from its twin to see the result.
If you do not know how to download MP software properly, it is DANGEROUS to your machine.
The float valve is stuck.
There are 2 possible causes:-
1. Touch Screen sensor of Dynaview fails to provide correct position.
2. The MP software of Dynaview is corrupted.
I would recommend to download a new MP software...
What are the major causes for TRANE CHHC Screw Compressor motor burnout?
Can I have sb0041 to study?
The carrier chiller model 19XL5353304CR S/N 1994Jxxxxxx has an intermittent alarm.
The alarm message in alarm history is
'CMPD 221.0 F exceeds limit of 220.0 F, Check Discharge Temperature'.
I work on one 19DR machine that has High Discharge Temperature trip.
We ran it for 2 hours and have the following data.
The oil temp is 140-145F. The suction superheat is about 4F.
The left side of Digital I/O Board is called Digital Input (DI) Lines and Right Side called Digital Output (DO) Lines.
The Control Point (CP) is the software program that drives one or more Digital...
Please! email me York form 450.20-NOM1 and BACnet Microgateway Operation Manual (450.20-??).
No email addresses in post
Please read site rules, Thank you.
Can your guy email me TRANE CTV-SB-48?
Thanks in advance
It is York YT 300 Tons chiller. There is no tube leak. The tube sheet leak are at both ends. Is it recommended to do tubes eddy current test? What is the estimated cost?
We found the leak at water cooled condenser tube sheet nut tubes.
The water inlet pressure is 70 psig. The chiller refrigerant is R123.
What do your guy do to repair this kind of leak at tube...
I think so.
Check your email.
Djken, Can I have your email address? Removed email
Please put email in your profile!
Check your email.
For those who have it, please kindly email me. My email is in my profile.
Please send me an e-mail.
My e-mail address is in my profile.
YORK "L" is ISO 120 POE Oil used with DXS Screw Compressor on YCWS/YCAS Chiller.
If blank screen means dark, check the cable from Micro Board to Inverter Board next to the Display or the display lamp is poor.