Type: Posts; User: danish
If we know just the chiller cooling output in TR, can we calculate the chiller flow?
I tried a lot but I never succeed, I can control deta P by DPS and secondary VFD pumps but to stop LOW return temperature back to chillers/Hex never achieved.
I believe the only thing we can do is...
In a typical Heat exchanger (chilled water) system, in secondary side I have VFD connected pumps controlled by Differential Pressure Sensor.
How could I improve delta T?
How to make sue that cold...
thanks. but do I need to include all the motors including cooling tower?
How to calculate COP of water cooled chiller plant? What are the fields required?
Thanks to all of you...
I have water-cooled chiller, I need to calculate its cooling output in KW. I have chilled water flow in GPM and supply & return temperature in C.
Basically, I want to have an open protocol (BACnet) BMS system, so other systems (e.g Fire Alarm & Security system) can easily be integrated.
Hi, I am looking for BACnet DDC controller with open protocol for intergration. Is BACnet IP is open protocol or BACnet MS/TP?:)