Type: Posts; User: HVAC dawg
my bad, sorry. read it wrong.:whistle:
Did you check with the manufacturer
Just like you ancestors, head west.
If there is a leak, you would find it right then recharge the unit.
what's the charge on the unit?
30 yrs wow let's think whats your opinion and let's figure this out I've been in the field 4 yrs whats the indoor temp and what the ambiant temp?
Go with the Lennox 95%, I just installed a 97% fully modulating furnace and it works really nice.:grin2:
Should have the specs in manual!
What is the blower closet do mean the furnace in the closet?
I'm trying to get a better picture of the location!
The large return is in the closet on the 1 st floor as well as the other one in the hall 4' from the T-stat?
How many Returns are in the house?
What type of system are you using currently?
Is this an upflow furnace, with the filter rack below and your return can below that?
Usually get in the Truck!
Has the high limit been checked?:grin2:
Could maybe be hard start?
I would possibly concerned with the pressure drop.:whistle:
I'm curious because of what you might end up with if you tried it? And what your use for it would be?:putergreet:
What do plan on using it for?:putergreet:
Whats the application bra?:putergreet:
:cheers: Sweet, well like I is that what the parts are rated at?:whistle:What's the weather like down there?
:putergreet: Did I miss something? Are you in Guyana? Where is that exactly?
I'm only seeing a .5 ton difference and if you went with two ton all the way, why wouldn't you want to?