Type: Posts; User: PPettigrew
Search: Search took 0.00 seconds.
Is this a new unit? Has the unit and duct been sized correctly? Has it been balanced?
At 57HZ you are at near full rpm of the motor. The VAVs are full open. Could the fan be loading up too much and spinning/skipping the belt? Did you take an amp draw of the motor to see how loaded...
I got my start as a young boy going to job sites with my Dad. Then I started working in the warehouse/ parts runner and doing helper work when I was 18. I would help on installs of new equipment...
Hello. My name is Paul. Been in the trade since 1989. Looking forward to learning more.
Results 1 to 4 of 4