Type: Posts; User: 381engineer
Search took 0.02 seconds.
No you do not need to be a dealer.
Just give them a call. http://www.loytec.com/about/contact
You should look at the Loytec Bacnet products. I'm guessing a LINX201 server or maybe one of the LIOB Bacnet controllers would take care of your needs.
I just completed a week long training for...
If you run smart installer you should also be able to upgrade lonwatcher (for free)
And I do believe it will tell you what plug ins are installed and what needs to be updated.
You will still need...
Sounds like the plug in is not registered for the device.
You could also run Distech SmartInstaller and it should tell you if there is updates available.
You would still need to register the plug...
It sounds like you are highly motivated to save energy.
What percentage is HVAC of total building usage?
What about lighting and plug loads?
Have you evaluated the rate structure?
Ask for Frazier
Open up a points browser and look at the VavObject function block.
Find nviDuctInTemp and nviWaterTemp. You may need to write a invalid value to one or both points (621.806)
Double check the...
Really dude FT-10!!
Lonworks is a well defined standard. If you follow the rules it works.
Sorry to kind of hijack but I'm curious and I'm sure others will chime in,
but what is the advantage to what the customer wants, is there some mechanical improvements going on or do they just want...
Do they have them in BACnet:grin2:
I am partial to the Circon VAV controllers.
but all their ASC controllers are worth a look.
And now they have a graphical programming tool for their big programmable UHC400.
And if you do LON...
Circon is not out of business.
Give them a call.
Ask for Mike in Tech support.
I did the exact thing you are talking about 4 years ago and things turned okay for me.
I had zero controls experience going in.
But....you better be willing to put in some long and unpaid hours....
I did speak some more with Daryl from Loytec concerning this post and because I don't have any experience with BACnet.
He said they put the wireshark tool into the LVIS precisely because...
You should look at the Loytec LIOB Controllers
IP based controller with ability to expand with additional IO.
BACnet or Lon,...
I've been told a this is a nice unit.
Concerning past Bacnet issues I can't say for sure if they are resolved but I bet they are or will be soon. I know Loytec has invested a lot of effort into their Bacnet line of products.
I'll see if I can get my propaganda updated.
A couple of thoughts and suggestions.
1 – Can Distech controllers of hardware version 6 be upgraded to be Freely Programmable (i.e. so that they use the Freely Programmable LNS Plugin)?
A good book.
Our very own Lonboy is hosting a Lonworks training class in SoCal
He could be a good...
You should look at the Loytec L-GATE 950/951Universal Gateway
I believe this will work nicely.
Have you tried lonmaker or other LNS tool yet?
Sorry in advance for a slight hijack.
i just took over two building with the same controllers and I've got a large number of controllers where the airflow readings seem to read way low.
I know I missed some of you guys last year and I hope not to make the same mistake this time.
So... who's coming?