Type: Posts; User: miller-cold-filtered
redungculus. can not be true.
for sure misse wired. yes communication too is the problem.
1 make sure condenser is clean
2 make sure there is no restriction of the refrigerant flow
3 is condenser fan running?
if you answer yes to all of the above then replace the overload device and go...
1900 sq feet with a 2 ton system? no wonder he is not happy with the air flow.
looking for document for a package gas/electric unit. not sure about the model #, pgx03605-1ab. any input will be great. search goodman web site but no tech doc. as a matter of...
need help with info. i need to replace a condenser by day & night with model # acr 9b 223 S/N 0660-13865 but not sure about the size. any information would be appreciated. thanks
just tried the trane websit. where is the english version?
need know what tonage in this trane? im guessing its a 6 ton. any input would be appreciated.
S/N : p41102345d
dude thats strange. i personally did not run into that problem but my uncle installed one in tx, houston and has the same exact problem. if the front cover is on then it would not work right and no...
ok i look at the 404a pressure chart. if your gauge show 10, accord to the chart is around -30 no? and your probe show 31, something is not right. isnt SH is out of wrack?
your are killing me. i caught myself laughing out lound. this is not right! stop it already.
you think its defrost?
did i miss somthing? i dont think it gonna work even thou put in a new matching coil. the area is about 1390 (790 + 600)sq feet and a 2 ton coil??
COMPRESSOR DRAW 50 AMPS?
this could be the guts of the compressor even thou continue is good. pretty much let it rest in peace.
when u say that compress started but no pumping? so if you have your gauge in and start up the unit, the gauge did not move at all? what are pressures?
LG is coming strong. dont be suprise that LG make many parts for Kenmore, Maytag, and Whirlpool now today. getting a front loader is a plus in many ways that are already in this thread. the only...
looks like you are in a jam jat. not a good idea for cooler box or freezer box to be right next to a fryer. it is tough to mantain cooling temp when you got hot and greasy air right next to it, not...
yes your are right. if you use direct fresh air to supply your hood then the air is about the same temp as the outside air. for restaurant hood makeup air usually do not have that...
i know it could be over kill, but i usually tell people dont plug it in until the next day. just to be safe. that way you wont be wondering is one hour long enough.
some pixs would cool
i would not get a carlyle compressor ever. unless i let the owner know in writing that there is no warranty and im leaving the country soon.
about the tech support and customer service, i conqur....
agree with work on makeup air.
the hood make air thats coming should be cool and not hot air. if you got hot air coming in thats your problem. check that air and we shall continue.
as the building owner i would be focusing on safties. leave the cooling and heating for the pros.
1. make sure the roof is solidly strong. not just enough to hold 400 lbs or a 5 or a 10...
i would recover first because you already know that you over charge the systm.
second, i would check the blower motor. make sure its compareable with the old one. look at the horse power and rpm,...
get a pro or 2
one thing for sure, not going to cheap.
given an office, what size?
given 40th floor, how many windows?
what kind of R ratin?
possibly under size
well, from what i can tell is that the plentinum is insulated but the spiral can't really tell. some say it should be insulated for commercial and some say not neccesary. so, i can say for best...