Type: Posts; User: macheating
Search: Search took 0.01 seconds.
Contractor stays in and the fan stays running, company terminals shows open, its a fixed orifice system, could the problem be there?
brand new set of hoses and manifold
it does have valves, thats how i read the pressures
Head pressure does not move off of 150, comp runs for bout a min, suction drops to 50, internal overload takes it out
Having trouble with an ac unit, need help!!
Results 1 to 4 of 4