Type: Posts; User: protechplumbing
Checked vigorously for leaks during nitro pressure check and evacuation. No leaks, no doubts.
I applied for pro. The system was under charged. It's working great now. As I said, I think I moved the hose when I zeroed the scale so it was reading low. I slowly added r-22 while checking...
I got it dialed in now. It was low on charge. I must have moved the hose on the cylinder when I was zeroing the scale.
I added refer. Sh currently 30
80.1 intake grill
72 wet bulb
89.3 condenser outlet
piston metering device
That takes several weeks. I'll have it figured out by then.
I'm going back out there now I suspect the charge is some how low but I don't see how because I weighed the charge exactly. The line set is 25 feet long roughly and I weighed out the recommended 72...
Customer called and said in the middle of the night the unit stopped cooling and the suction line was covered with ice at the heat pump all the way to the compressor.
Heat pump was just replaced...
The main issue with them liming up is that when they draw water through a coaxial fitting at the bottom of the tank they picku sediment in the bottom of the tank. This sediment then clogs the...
I was referring to this link: http://www.renewability.com/power_pipe/index.html
Perhaps it is you who should be doing the thinking. Legionella will grow in potable water that is allowed to stand...
I also here that propress isn't good for application that are subject to constant vibrations. A voper compression system seems like the worst place to try to use propress.
I wouldn't think it could handle the pressures and temps in a 410A system.
Thanks for the info.
It would be faster but the material would be more than threading BI.
To be clear, you won't see cavitation in gas lines, only water lines.
I have seen cavitation in copper pipes due to not reaming cuts made by copper cutters. That will happen no matter what kind of...
Should I be looking at an open loop pump and dump instead of closed loop?
I can always replace the coil if it gets fouled. My only concern is energy efficiency. I can punch 2 holes in the ground...
At high water velocities if there are any imperfections in the pipe wall cavitation will occur just behind the obstruction.
uhhh, what? water expands when heated not cooled.
What do you have against propress for gas? I wouldn't trust it for potable water lines due to chemical attack and cavitation, but gas? Sure.
bad expansion tank?
The best thing to do is buy a larger solar tank. Look for tanks designed for open loop solar applications. They will have 5 ports on the top and 3 dip tubes. You usually get more mileage out of a...
sorry, i forgot about the price thing.
At 300' bore per ton, I would be looking at 1200' feet total for a new 4 ton geo system. I'm not sure going geo would be an economically sound decision in my situation. I would estimate that the...
If sized properly a single tank is just fine. You simply disconnect the lower element and leave the upper one attached. The upper element will only fire when you are about to run out of heat...