Type: Posts; User: kytech77
sounds like your combustion is plugged
its very possible to have another faulty defrost board. Have had any power surges? I would definitely get a quality technician to diangnose. You are correct, this is not normal
is your outdoor coil dirty?
make sure the sensor is in the correct place on the coil
ok...and you ohmed the sensors correct?
depends how thorough the rep is
If i had to guess.....I would say it is extremely overcharged
The Infinity (Carrier) is hands down the best system out on the market. Ive installed a ton
try moving the < No DIY instructions >
If you installed a heat pump your electric bill will drop tremendously
definitely compare warranties
we use to go 150ft. That was causing us problems especially with the entering water temp.....so now we go 200 ft deep.
We also use methanol here in Ky..... like he sail, basically antifreeze.
i havent seen anything that will touch the infinity yet.
could possibly be a board issue
sounds like a board issue
I was on a call today and the furnace is shutting off completely (everything) after about 2 minutes of run time. I'm pointing to a faulty control board. I have to go back in the morning
i agree, right tools make the job alot easier-faster
as long as the opening size matches the ductwork size.....its only gonna pull the amount of cfm as the opening of the furnace regardless.
definitely the hybrid, not all electric
in my opinion, seems the republicans are the idiots.....putting our great country in the spot we are today. Especially the last 8 yrs of hell....DAM REPUBLICANS!