Type: Posts; User: PowerPlant17
Search: Search took 0.01 seconds.
Yes it has a sight glass/float on each receiver, not showing a level. Valdelocc your right after thinking and checking a little closer it has a check valve between the receivers and condensers, so...
No cooling call. Compressor hotter than…. Low side 10psi High side 100psi Low amps on all legs 5.9-6.0
Nameplate run amps is 10
At first it looks...
01-01-2010, 01:23 PM
Update on pilot failure. Almost 48 hours and no failure. Adjusted pilot gap from 3/16” to 1/8” and raised pilot gas pressure from 2.5” to 3.5”.
Doubleduece the new stainless steel mesh burner...
12-28-2009, 10:03 PM
Both pilot and main flames. Both look good to the eye also. Pilot lights fast when watching it. No delay in it. Just like it should. Thinking maybe something with the factory wiring. I just don't...
12-28-2009, 08:09 PM
Flame current is 5.0v
I assume when you say try adjusting the pilot for 5v you mean adj. gas pressure and air pressure because maybe I overlooked a different adjustment that I can do.
12-28-2009, 07:54 PM
Yes sealed combustion.
Cabinet Air Pressure: 1.17"wc
Pilot gas pressure: 2.5" wc
Gap is good. Thanks for information
12-28-2009, 04:52 PM
Honeywell RM7895 C 1020 Relay
Application: Domestic Hot Water Heating
Control: Digi-Span Model: TSC/TSR (Two Stage Set Point Control) for 2 PK’s
Set points: 138 deg. 134 deg. 4...
05-30-2009, 07:53 PM
First guess is that it's being used in the wrong application. Oversize will kill.
Thanks, have looked there before and just looked again and can't find it.
Looking for a copy of York’s Microgateway installation & operation manual FORM 450.20-NOM1. I have them installed on one YT Centrifugal Chiller model YTK7C7F1-CSJ & one YS Screw Chiller model...
Results 1 to 11 of 11