Type: Posts; User: GOG
Search took 0.01 seconds.
inverter temp exceeded. 5 different machines in same plant.
got to be a problem carrier needs to address.
any info appreciated.
The real problem with this unit , is why the slide valve is at
Step 0 and the compressor runs @ 70%. I have set the current
Limit to 60, it runs on current limiting but does not unload to
Thanks for your interest, I have tracked down the sequence,
9675 , enter, function, oper data,.
It seems what I wanted was the service
Mode and I tracked it down. All is good,
Except the unit...
I have a millenium panel and would like to know how to get to the service mode menu?
I used the 9675 code and entered it , the panel reads service mode enabled but I cannot get to any menu.