Type: Posts; User: eliteair
Under 300 furnace would be under fired
325 is not that bad, as long as it don't go over 400
If you pull the board on the furnace, where the main plug is on the board you probably see the solder bad on the back , had 2 doing same thing.
You might need to check if first tech has manifold setting in the furnace correct!
The heat shild in the heat exchanger is rusted and falling down in the does that warrant a bad heat exchanger
Txv head 404s 502
60" cap tube
Just found one with a crack in the header,and a crack in the inducer bracket that hold the inducer motor will put pic on.
chicagojonny, what do you mean by the button in the middle?
Joehvac25, how can you tell?
Maybe someone cooking meth
looks like a goodman to me too.
is that the plenium? lol
:playing:Maybe the water was turning the fan blade.
CV/HP Programable Zone Sesor
( Zone t-stat)
M # BAYSENS019C
Head pressure Kit
silver tape on gas pipe, air handler setting on old furnace lower, no filter, etc ,etc, etc. tell me a heating and cooling co. did this:eek2:
Hey zapy, you come on here ON HVAC TALK and post something about not trusting us. MAN i will tell you how to fix the compressor here is the list of tools you will need...
1. BFH with long handel.....
We do work for ahs and we get paid in 7 to 10 Days so im ok with that.
Hey: Intechbill what do you me warrinty for finance co?
one co. around here dont use pipe dope on any of the installs they do. :eek2:
That gets a ( HELL YA!)
I think that the units are trying to sneak into the window!
If it holds water, it should hold freezone!:eek: