You need to change the t-stat cable to twisted, shielded 18/3 and ground the drain at the VLC. If it isn't grounded you'll see temperature fluctuations and/or the Microset will reboot itself every...
Type: Posts; User: kailuairon
Search: Search took 0.01 seconds.
Results 1 to 2 of 2
Used Equipment - Buy, Sell, Save!