Type: Posts; User: sr20detb13
thanks a lot guys
well can anyone help me out with a forsure? is the head pressure less due to the way the unit works? do you usually only check suction?
partially gas and liquid, thats what i was reading. thats why i didnt want to follow the text book pressure data. im not sure with these new systems.
Ok this is my first real post on this forum. i am certified in 410, but havnt been in the field for awhile. This is a super new 40,000 btu mini split, with dc inverter. So heres the run down. leak...
this sanyo is pre charged with 7.9lbs and is good for 10-100 feet line set. just needed to leak check, vac lines, and test run. And runs awesome.
yea i found this out last night... the line is sitting with freon in it, with not enough insulation and its just getting cold..
I'm in the middle of my first ductless mini split install, so i took some temps in test mode and in full cool. temps seemed alright but I did noticed that after the system was just running the fan on...