Type: Posts; User: ClassicDave
Search took 0.03 seconds.
sounds sort of like my problem,
system 5 yrs 3 months old, compressor out of waranty:
No Cool Call:
had a bad capacitor, replaced and left. Two hours later called back not working. Went back...
I pulled the refrigerant back using the compressor, locked it down and pulled the disconnect to the condenser and shut off the breaker to the air handler.
I took the old txv out, put the new...
went got a txv replacement.
Got to customer's home, pressures were 25 suction 205 discharge pressures.
recovered refrigerant back to compressor, that went well
removed txv, cleared...
Weather King 3 ton heat pump, R-22 Bristol compressor
system not cooling, 5 years of no issues.
Found bad capacitor replaced capacitor, rheems plastic capacitor bulged on top, replaced cap...
I do a lot of zoning and I fix a lot of other attempts at zoning.
My favorite zone control is the Bryant Evolution or Carrier Infinity Zone Controls with their communicating system....
Actually there is only one difference and it is in marketing
The Carrier is a National Consumer Market, while Bryant is a Contractor Dealer Market
There is only one difference between the two on...
A pretty good summary. I can't disagree too much, but as you might have guessed I do have some comments.
1. The HC16 and the Carrier Infinity or the Bryant...
The Perfect Air Purifier produces only around
5ppb (parts per billion) ozone. The EPA recommends no
more than 50ppb for a healthy living space. In most cases, the
ozone output will be below the...
Definitely look into a system that at least qualifies for a tax credit.
Most important, the systems that qualify get you out of a RNC (residential new construction) models. Many A/C guys love...
If you have purifier, remove all other filters. The purifier filter is the only filter that should be used. Any other filters being used at the same time more than likely will cause high static...
There is always the other option.
Go with hybrid heat and qualify the tax credit under heat pump.
Heck as long as you get an Infinity Furnace 58CVA and the Infinity controller you can then choose...
on #3 it says
A Manufacturer’s Certification is a signed statement from the manufacturer certifying that the product or component qualifies for the tax credit.
I have not seen...
The thing is and someone may answer the question, what is exactly a Advanced Main Air Circulating Fan? To me it is not a variable Speed Fan Motor in a Furnace.
I could be wrong though.
Well since this post is old, and the original poster is probably enjoying his Bryant.
So I would have to agree that Bryant was a very good choice! :D
95% gas furnace and above,
Sorry 80% is a no go.
next the truth to the Weatherization Deal,
you want to look, how much you made this year.
and what your taxes paid or received was.
Tell your hack, you want a Bryant Evolution Hybrid Heat System with the Evolution Controller!
They are sweet! oh he probably doesn't know how to hook it up because it is over 13 SEER.
What is the temperature when Celsius and Fahrenheit are the same?
Times up, you lose!:p
Learned that in the 5th grade from a bonus question we all got wrong! Amazing I still...
5 Ton Ultra High systems drops tremendously in effeciency compared to a 4 ton.
If you can go with a 4 ton that is the way to go. Plus most ultra high efficiency systems need 1 1/8 suction copper...
If you can fit it go with the FE4ANF006 gets you a better SEER and HSPF rating.
If the dealer is going to go up only 500 on the 19 go with that. 19 has a varable speed condensing fan motor and 2...
I sent the guy an email.
Felt sorry for him after I found the closest Bryant Factory Authorized Dealer was 90 miles away, no Factory Carrier Dealers to be found. Only 2 Carrier Dealers with in 20...
SEER rating should be upgraded.
I like to see a $2000 consumer voucher to be applied to a 2 speed systems that meet 16 SEER or higher.
Talking about saving energy in the USA that would do it....
My system is a 12 SEER Rheem Heatpump
RBHA-21J11NFGAI Air Handler
TXV indoor Evap and TXV to outside Condenser.
Roughly 8yrs old.
I'm going to post...
I have a similar situation
many have stated the txv in the condenser to be the issue.
I have ordered a TXV for the condenser and will be putting it in on Friday.
Doesn't matter if it works or...
Take this post above seriously.
I am changing out a TXV on my mom's rheem, just ordered it.
I have extensive experience in zoning. I also fix a lot of messed up zone installations.
Believe it or not, It really depends on your design of your home. Attic Space, where the Air Handler is...
Spring and Fall is Rebate Time
When things are Hot or Cold the Temp sells them.
Spring and Fall is when manufactures do their rebates on high end equipment.
And it does save customers money on the final price.
Factory Authorized Dealers Carrier and Bryant can give the...
I would wait, there are thermostats coming out in a year that you can up load your pictures.
So it will be a digital picture frame one minute and your thermostat the next.
Not sure if they will...
4000Kw a month? Way too much! Unless you have some plants growing in your house you are not supposed to be growing.
What is the set point temperature on your thermostat?
74 is the highest...
GEO Thermal ground is not beneficial in Florida like it is up north.
GEO Thermal Water Source is, but the problem has been the discharge of the water.
It's just seems to become inconvenient over...
I'm on the Bryant side, but these systems I install 90% of the time to my customers.
So I know them pretty well.
There is a different noise, the hermetic has a little more higher tinny sound...
My knowlege they are not the same. The Jacksons are a retro fit to the carrier/bryant zone damper and cost a bit less. They can be used with Carrier/Bryant zoning so they will work.
You seem to be basing your decision on a low price.
You will pay for it in the end.
If Johnny on the spot you trust then tell him you want a quote for
XR14 with 410A...
Freon Temp relates to Freon Pressure
Freon pressure/temp is guided by the manufacture design for proper heat transfer to maximize efficiency of heat transfer.
It's a Balance of this Surface...
The High limit switch over rides everything, thermostat won't work.
ah ok, happens when unit is running,
Does this board have a code for high limit?
now here is another option for the tech to...
Get some estimates your biggest concern between the two is the contractor.
Are they Factory Authorized-Carrier, Comfort Specialist-Trane
I personally like the controls in the Infinity but you...
I'll say I had no clue on Hydrokinetics.
Had to read the post below
I guess the thing from that post is will the customer still get off...
Yea, you need to call the installer back.
The system may not be working correctly and it is less than a year old.
Everything is under warranty.
This may not be the problem but its a starting...
That is a key point to find out,
Does it give the error code when the furnace is running or when it tries to start.
your furnace blower running like the high limit switch had been tripped is the...
there is a problem,
first if he replaced your reversing valve that is the most difficult part on a heatpump to replace. I would have made a big deal to goodman with hopes for a new outside system...
Twinning means two furnaces tied together that act as one bigger furnace.
Normally it takes a twin kit. So your code really is ment as the second option.
24v phase problem, which normally means...
I'm a Bryant Authorized Dealer, which is the same as a Carrier Authorized Dealer. I know every combo there is and I have my own opinions of what I recommend to my customers.
First the salesman...
You should be charged for a service call from both companies.
These companies gave you great customer service.
Once you decide on a system then they can discount the invoice off the system.
Customer should have upgraded from XB to XLi
I had a customer once that heard a high pitch noise.
We changed out the condensing fan motor, put a compressor blanket on.
Put Condensing vibration...
I'm also looking into this,
I heard if you plan on living in your home for more than 5yrs and you can drop your interest rate 2 poiints or better it is worth it.
It's around $3800 for closing...
Cheers to a Healthy Lad!
It great to see a proud grampy googlie eyed over his grandchild.
Now you can play with toys again!! Just make sure you share with your grandson! Yea!
Have the original Heating Contractor come out and explain the furnace it to you.
1yr Warranty Parts and Labor.
Manual J is not pin point exact.
It is a tool to give better precision...
Always wondered how Trane makes the porkypine coil,
Been to Carrier/Bryant Manufacturing plants interesting stuff.
The biggest thing I got from the tour is how they solder the...
You should really call the service company and let them know your situation and if the tech was just out there then they shouldn't charge you to re evaluate your problem. They need to know that the...
What Model 286A or the 288A?
First outside Temp must be less then 50F
If you set your interval at 30 min then the interval check will take 30min if the sensor reads 32F or less it will go into a...