Type: Posts; User: chow foon
Magnet wasnt too bad . I got it going b4 I clean it
Put in new bin switch . fires right up . but how did it fail because I turn it off ?anyway , its working . watch it made 4 batches after I gave it a clean . thanks again 2sac .
No codes . I looked many many times . but the bin light would cycle on and off when I move the damper . checked all electrical connections already. Will go back to clean the machine + check on bin...
Under counter unit QD0132a won't go into freeze . original complain was low ice production. Adjusted itp . turned it off to check flow valve . turned back on . now won't freeze . only water pump...
my appion core tool leaks .. i experienced the exact fluctuation at least 2 times with the appion core tool , now i just wont use it
You r a good man dawg :bump:
ditto .. Makita is the shizit !!!
mine was easy , i met the coca cola guys , had 2 guys lift the ice machine up, they slide old one out, slide in new one in, they didn't even really need me there..
Thanks ! Coulda use one yesterday
where can i get one of these svom 18 ? i searched everywhere .. but can't find nada ..
Take it to your local supply house . Cost u a few bucks to recycle it
do u mean recovered ?
thanks a lot fellows
take the whole machine down then put on top of new machine
howdy, I'm fairly new to ice machine and refrigeration.. was just asked to disassemble an ice machine on top of a coke machine till coca cola swap out a new one then put it back .. model of ice...
im not exactly sure now . but i got 50 after i reset it. can't remember exactly if i reset from the control board or interrupted the power .. shrug
its kinda rusted , but i couldn't see any cracks .. replaced hx in one of the units last year .. they r pretty easy to spot ..
thanks for the heads up.. already removed 1 return plenum to a cooler area ..
58 or 59 is gas valve not energized after 2 mins . because the main limit is opened due to over heating in my case .. u could either reset on the control board or open the disconnect . i got a 50...
u will get a 50 when u reset the main breaker when u get 58 or 59
so what happened was the returns are located at about 4 feet higher part of the ceiling.. so its like a hot pocket that provided 90 + degrees of return air , bumped the supply up to about 140 deg ....
i am experiencing the exact problem/same unit.. found my fan belt was extremely loose .. plus the blower motor pulley is pretty worn out.. fan blower pulls 6.6 amps .. fla 10 amps. changing out...
Goodman can supply u a piston for your 3 ton 10 seer condenser. For like $ 6-7