Type: Posts; User: stephen mendoza
Search took 0.02 seconds.
Found the problem. The strainer right before the water pump was clogged.
Scrubbed it out and it returned to normal.
I have a boiler hot water loop in a building. It cycles over and over
constantly. I see the water out going temp. jumps up to 160 degrees and
then drops down to 140 degrees. The water...
I have a 6 story building and I have air trapped in a
hot water loop. 6 fl. and 5 fl. coils are fine.
On 3rd fl. the coils water runs out cold. I have
air trapped between 1st and 4th fl. ...
Are you talking about the green bulb that bleeds out
air on it's own?
The outside temp. brings on the boiler, I have that set
It's natural draft. Water tube. temperatue cycles the
boiler. I recently replaceed the flow switch. Could the
paddle posably be stuck in close position and keep it
I have a boiler making a loud howling noise everytime
it heats up. The water temperature rises up and down
constantly to 180 deg. to 120 deg. My water pressure
is at 12 psi. Is the temp....
What is the whole point about the expansion tank to
a boiler? Is it to keep air out of the system?
If I have 12psi of water going to the boiler, when it
heats up will the pressure rise?
I have a building that puts out constant heat during the
winter. The outside stat brings on the boiler and the fan
boxes for the coils. My RTU is constantly putting out
55 degrees to the...
I have a VAV box with a boiler coiler in it with a duct
supply of 55 degrees. How hot would the coil need to be
to get a 100 degrees out of the runs?
Hello, figured it out today. I had a guy find that the HP
switch was cutting it out. A bad switch. It is a little
low on freon. Sorry I didn't have that much info but
thanks for your...
Hello, I have a Mc Quay unit that has two circuits on it.
Each circuit has two compressors on it, 6 stages of
cooling. My problem is that the #1 circuit trips out on me
and I have to turn...
Thanks Turtle. It worked.
I have about 66 supply and a 78 return. It seems when the
day warms up to much I'm losing. My pressures was 82 Low
and 275 high. My UEI meter on the suction line read 48
degree temp. ...
Model - CKL24-1F
Serial - 0306424230
How do I figure out tonnage on my unit?
I have a low side sitting at 90 psi and high side bouncing
back and forth from 200 to 500 psi. The compressor amps
is bouncing back and forth from 5 amps to 10 amps and it's
rated at 12.1...