With a Data Aire system the sub-cooling needs to be correctly set for proper fan operation. The sub-cooling needs to be between 8 and 10 degrees when using a P-66 or P-266 fan speed control. Unless...
Type: Posts; User: blueridge2
Search: Search took 0.00 seconds.
Results 1 to 3 of 3
Used Equipment - Buy, Sell, Save!