Type: Posts; User: lontshooter
Search took 0.04 seconds.
One of the things with the shell command in Hyper terminal is you need to have the proper settings to connect to the shell, those settings are:
Bits per Second: 115200
Data Bits: 8...
IF you could give a little info on the system, I would be able to help you out.
Is there a time schedule or is it a ATS attached to a point in the system?
What is the main...
Been busy and not alot of time to get here, but here it what you are encountering with those inputs.
They are ave inputs, but they scan only a small number of inputs on the ave then...
My position is that you can use any good open protocol you want.... or you can use Lon or Bacnet. Doesn't matter to me because in this changing world you will now have to work with both....
The easy way to clear the device and redownload the sav file to it is to use the red button on the board to reset the controller and power it down and power it back.
Reload sav file for...
I am intrested in the MR88R-C, shoot me an email in my profile.
I am with you on this one also. I had to replace a E3 with a SS2.0.
I ran into the same issue that you are having.
Make sure that you have the CS4 release of contribute to work with, you...
The big splash will be at ASHARE in Las Vegas for the software which will be name StructuredWare on the Wonderware platform.
Lots of engineering time is going into this product to make sure the...
Have you tried leaving the username and password blank and just hit enter.
Then the next would be username: admin and password: leave blank
Then the other one is username: user...
You have mail.
Is there a limit to length of Lon wire ran from stat to stat?
Go to this link and look at page 36 & 37, but I would read the whole document as it will help you out.
I have had one issue with that stat and about the same issue that your are having now.
First thing that I would be looking at is the stat and if the XIF file is loaded into the stat...
You've got mail
You've got mail
Any programing or control of an Invensys/TAC system is done thru Workplace Pro and Workplace Tech.
There are two sides to Invensys/TAC, one is the LON side and the next is BACnet.
First question are you using a router or switch that your computer and the LIP are connect too, or are you connected directly to the LIP from your computer?
The default IP address for the LIP is...
Crestron uses what they call Crestronet for there commnication format.
They will not talk directly to any device other than a Fieldserver device.
They have agreement with Fieldserver to produce...
What are you looking to Integrate with Crestron.
Have done a few projects with there systems.
Most common communication is either RS-232 or a LAN connection, but there are...
This should help you out to resolve your issue with the controller.
Need to remember that you can not retrieve the code using the new GFX programming software.
You need to use the...
Couple of question for you to allow for more help.
How long is the run for the main trunk line from computer to farest device?
Are there already repeaters in the line for the...
Do you have a copy of the SAV file that you can email to me and will look at it.
Well I have heard the rumors running around my area also.
The Delta guys out here have been told to keep a lid on everything and not talk about JCI and Delta.
If JCI buys Delta, it will give...
There is a file installed with some of the newer programs for checking you licensing status, that is called FNP Licensing Service.
It is common to Adobe software.
It was design to check the status...
You need to get the software Workplace tech by TAC version 4.0 and better, to be able to due balancing on the Micronet controllers.
The software is properiatary to TAC(oops!!!!) Schneider...
SNVT_time_stamp#LO: text(date(year, month, day), (" "), time(hour,
It is how the time stamp is defined see above.
This would be from a controller that you want to...
The 203 model has 3 Universal outputs and 5 Triac outputs.
Make sure that you have your fan DO on a Traic and not a UI.
Check the setup of the Point in the program of the GFX, also...
Have done a few installation of the Spinwave sensor in Hospital ER rooms and operating rooms with the use of just one repeater in the system. Have also installed in X-Ray rooms with lead line walls,...
There is no known driver in Tridum for INET2000 or INET7 system.
The only way that you may be able to make it work is with the OPC driver for INET, otherwise you will need to install a...
Like Carb says, check your subnets first to make sure that everything is on the same subnet address.
The scanner that Carb recommended is one that I use also, works great for all BACnet device on a...
Two things that come to mind,
First thing is that Andover is part of Schneider/TAC and the software for programming is properitary, unless you get the complete software package with the system....
The first thing you need to know is this a computer based web server or a device based web server I.E. ILON100 or ?
The second item is if it is a computer then that would depended on the...
Go to the follwoing link and it will help you to indentify the SVNT that use are using, along with the properties.
This should explain what you need...
Could this be a Tridum killer in the works if it does show it's head.
The first thing is that you need permission in Vista to allow the SQL DB to be modified.
The next thing is to remove any instances of INET7 including the SQL folder under the C:\ drive....
To integrate the controller into Honeywell, who need to know if the XIF was create in a Lon Management Tool, but the issue is if they use the standard xif file and did not update it...
If you know Wonderware at all, then you will know what TAC/Schneider is about to release with there new NSP platform.
The name of it is still in the air but sources say that it could be...
Are there any grphic page that show the operation of the system?
Take a look at the points under the summary page and see how many have calc's or other attributes in the system.
It won't be easy to...
What version of Inet are you using? Is it Inet2000 or Inet7?
What type of DCU's are you working with? Model number would help.
Any more information about the system will help also.
This is the one that I use.
It may be a little bigger than others, but it does everything that I could need in the field and on the test...
This out ot be an attenetion getter.
They took at LonMark ECC-VAV controller and as it says upgraded to BacNet, now if I understand Distech configuration correctly this is not possible for this...
Spent the time there and went to all of the booths at the show.
Yes Darryl was there and had the real only live working demo and hands on presentation of the show.
Spent some time with Darryl,...
I get in on Sunday to just enjoy the Show and good times.
Modbus IP would be better to use with the JACE box, the Modbus RTU will have communication issue with the JACE.
Make sure that when you connect the two togehter that you have the correct register...
One side of the TAC line is LON and the other side of it is Bacnet.
Which line are you going to work with?
The software for TAC is properitary and can only be sold to TAC partner, is your company...
Looking for usrguide or manual for this device.
Also what software is needec to program this device or is it auto-discovery when connected to the TUX backbone of the network.
The first thing that I would do will be to create a new network database and see if you can commission one of the boards in the RTU's.
If that works then the DB that you are using is...
The UNC 520 can integrate combinations of LON, Modbus, BACnet, or legacy devices with the appropriate optional drivers. It provides integrated control, supervision, and network management...
Looking for manuals on configuring Alerton BCM-TUX device.
How to connect to it?
I know that I need Envision software.
Do I need that to configure the BCM-TUX device?
Are the points that come...
The software that you need is propieratary to Schinder electric(formely TAC),
The software is only available to Schinder Electric dealers.
If you are looking to make small...
What seires controller are installed?