Type: Posts; User: Flashman989
anybody have service manual on simplicity controls and ZJ/ZR 180 thru 240:gah:
poteniometer on vfd board that u have to adjust off of chart with amp meter hooked up
yes pretty much
I was dispatched out of Tenn. which controlled Tenn. Ohio,Ind,Ky,Ill and 4 of us were top for longevity for that region
worked for CMS for 4 years
turnover is extreme to say the least
national accounts company,corp based in fla
also parent company areas holding,under umbrella,CMS,Nextech Northeast,Nextech...
work on liebert data systems all the time
first if high head is tripping you need to look at dry cooler,no or inproper air flow will trip HPS which is manual reset
compressor 1 will not stay...
not enough info
what is low side
sounds like restriction
also need people right now in ILL,MIN,WIS,IO,MICH,OHIO:grin2:
all national retail accounts
have nte to go off of which is good amout
best buy,kohls,tractor supply,gander mtn,burlinton coat,gabriel bros,all national retail and every account is different for...
:grin2:never worked for benner but have alot of guys with us that came over from benner and commercial air systems after they were bought out by lennox
all i can say is that we are in the service...
do not like running flex duct
would rather run sheet metal duct even in crawl space and if i remember correctly 3 ft of flex from main trunk is code for commercial alot of residential installers...
1. load calulation vs square footage
2. wet bulb dry bulb
3. temp. differance across evaporator
things u should ask as a consumer
75 degree return air,20 degree drop across a 40 degree evaporator...
anybody know anything about this company
based out of orlando fla and expanding north
thanks for the input I sure hope that I get the job or at least a call for second interview
Went to interview for JLL on monday don't know the outcome yet but site was for large corporation on there site 230 rtu's,chillers,boilers
there into property management for large customers listed...
Found out about the high limit for york tech service after unit fired up the bad thing was it was at a dunbar armored car sight with no windows talk about a customer having a fit then we proceeded...
Had a York start on fire on me last winter in heat start up mode unit running fine everything looked cool.contacted york and was told they had an issue with 6 ton and less with high limit not opening...
I have interview with them on monday for cleveland ohio will post more later
benifits on website don't look bad 1.5 pto days a month