Type: Posts; User: bighands
Search: Search took 0.01 seconds.
02-22-2006, 07:46 PM
Looks perfessional. Im wondering where the condensate trap on the a/c drain is?
Im sure you thought of insulation in a crawl? Is there a product that will be sprayed on?
I have a oL reading on my fluke meter in the ohms setting between common and start winding on a single phase compressor. Does this mean possibly the overload is open or is the compressor toast.
Looks like it's time for another condenser. A Carrier TZA Puron unit would look nice in place of that hiel piece of #!!#.
we need pictures on this website thats why it's HALL OF SHAME.
I cant believe some of the work people get away with.If i were the service tech on this job i would look to condem this product. Its in the best intrest fot everyone to replace. bighands out.
Results 1 to 6 of 46