Type: Posts; User: mikeacman
I thought about that
Not sure it would work because of the dynamics of the mche
the situation is this:
Trane RAUJC25 R410 single circuit micro channel heat exchanger condensing unit
Paired with a trane air handler with a standard four circuit fin & tube evaporator coil.
Mitsubishi multi city or daiken
One condensor ,mutupule boxes,fresh air available
I've had cracked ignition wire causing intermittent issues as the spark will go to ground before the tip of the ignition electrode.
I've had dirty ignition electrode assemblies allowing the same...
Pretty soon she won't ,
When she's dead or her house burns down.
Usually happens when brazing it in .
Wet rag or remove the eye when brazing and don't nuke it with heat.
how do I know this ...lets just say I do.
Other than that maybe contaminants
Misunderstood original post ,sorrry
125 sct on & 80sct off
Or use a modulating control to maintain about 90sct ,with a ball bearing motor preferably
may need to adjust those numbers but it's a place to start.
If you have a...
He may have burnt a solder trace on the board when he grounded the hsi.
If you have a call for heat and a pressure switch code I would assume the board is finished.
You hardwired the inducer...
Is the HPC on the discharge line really.close to the compressor?
Are your crankcase heaters working ?
Are you flooding back?
Most places you can't smoke inside anymore . Won't be much longer it will be everywhere
Why not just move her into the basement and take away her red stapler?
Why not a dedicated...
The old switch was fine .
The machine was like new ,only several months old .
Everything looked brand new and was in place .
The old switch worked fine with the new assy / magnet
trust me ,it was there . And it was in Montgomery....it turned into a long day
I can buy the argument for going back to residential.
Sometimes after humping half my truck a thousand yards ,to work on something heavy ,dirty ,a POS etc... I sometimes wonder why not go back . ...
I could buy that.
I suspect it is a man made magnet.
Maybe a dud.
I do know the old magnet was about 3/8 in diameter and the new one is about 3/4
No magnetic pull or anything out of the old magnet
Magnet is there. It just isn't a magnet anymore
Anyone ever see the magnet that makes the bin switch lose its magnetism?
Changed the bin switch first and it still wouldn't work,because the magnet wasn't a magnet...
Sorry about that ...
Read the manual ,it's a joke .
I've had a few of these apart ,once changed a fan motor ,once a pump and some other things .
I don't recall ,
do a search for the trane manual number in the post above .
Munch supply has a 2010 copy which should be current.
I would search "trane (the the publication number above) munch supply"
do a search for this , it's the newer book...
trane rt-svd03g-en .
munch supply has a pdf of it available
this is a link to an older manual which may not include any updates or changes , proceed with caution.
you may need the reliatel book
next time look here ,,,, enter the first 3 to 6 digits to search.