No you cannot...You can load up a wire to 100% but the CIRCUIT BREAKER can only take 80%. So for a MCA of 14.2 you will need a 20A circuit breaker which requires a #12 AWG conductor.
Type: Posts; User: Walleye82
Search: Search took 0.00 seconds; generated 31 minute(s) ago.
Results 1 to 1 of 1
Used Equipment - Buy, Sell, Save!