Type: Posts; User: mark 11
Search took 0.01 seconds.
I think TRUE has the best gasket design , just pull
old gasket out of channel, and press new gasket into
channel, no screws no hassle, why cant they all be designed this way, definitely easy...
I went back in 1998, made it a vacation combo with my
wife,checked out Atlanta, Stone mountain, any way the
Hoshizaki advanced seminar was pretty interesting, at
the end you get a tour of the the...
If they last well past the warranty replacement time
thats good enough for me, we dont want them to last for ever do we??????
When i get a customer quoting me my cost on parts or
equipment, i tell them ok ill install it at that price,
ill be back in evening with part,when they call in evening
to ask me when im coming...
Thanks for info NDFROZEN, it is amazing to see what
a difference new insulation makes, i once had a customer
with a 7 by 7 walk in freezer that would not go below 28
degrees, my dad sold them new...
I lost a replacement refrigeration system Job for a
Mcdonalds walk in freezer to another company,
this company installed new complete evaporator and
condensing unit system, i was there about a...
I once had white ice on a Manitowoc machine, problem was
burned out dump valve coil, white soft ice was from extreme
concentration of mineral build up in water............
Just include the time it takes you to go to the supply
house in your hourly rate, customers pay big bills
more willingly when they see it took you a long time to
fix there equipment, you can only...
Just wondering how many of you fellow techs have had
walk in freezer service calls in summer where every
thing checked out normal, super heat, subcooling, pressures
with in normal range, defrost...
Thank you very much for that information SNEW MAN 24,
im going to talk to that york counter guy in person
Monday and show him the print out of the 13 seer
one ton units he told me they dont carry...
Any body know where to get 12000 btu a\c condensing units,
bought the last one from Johnstone,[ discontinued ] i was
told York carried them but when i called them i was told
they dont, did i get a...
I wonder what a HeatCraft 4 blade blower evaporator
would look like mounted to the bedroom ceiling,
maybe just cover it with some fancy wall paper,
a could get very creative with a customer like...
The future belongs to the Scroll compressor,
lighter, stronger, better,more efficient!!!!
Ive got a liquor store owner customer with a Hoshizaki
ice machine with evaporator separation like that, its
bin filling the bin in that condition for years,
it is amazing how they will...
One huge advantage of having 2 completely separate
systems is the the odds of both of them breaking down
on a 95 degree weekend would be extremely remote,the
house temperature would be tolerable...
I had a customer that had me replace his 4 ton scroll
compressor with a piston pump just cause he did not
like the sound of scrolls, he paid full compressor
install price and i found a new home...
Thank you guys for info,end of long day, read it upside
Any of you fellow techs know what tonnage a 890 goodman
piston is rated at????? thank you!!!
Do any of you fellow techs know if a typical water
softener system will have any effect on your typical
commercial ice machine water filter, had customer
with home Manitowoc QM 30 ice machine with...
I worked on that same machine for a customer around two
months ago, same problem, it was a ICE O MATIC, same
machine with there name slapped on it, Ice O Matic
will ask double the cost for parts...
Any of you fellow techs using a ultra sonic leak detector
on a regular basis, had this sales man ive known for years
let me try out this DRACO DL10 ultra sonic leak detector
for a couple of weeks...
Update.......went to check on machine today, cycled off
on full bin, normal operation, it was old float assembly
sticking closed, im going to start installing new float
assemblies instead of...
IT is air cooled self contained, 40 psi flow pressure,
going to install new harvest float assembly to eliminate
possible intermittent sticking,any other ideas??? also
unit located in back yard of...
Hoshizaki KM 450 r22 unit, unit shuts down every day on
3 beeps,[ freeze back up timer ] installed new water
solenoid valve, cleaned float assembly, clean evaporator
coil and water...
$1000.00 dollars for crane rental? is that a Mercedes