Type: Posts; User: DCVoltZ
Search: Search took 0.00 seconds.
08-29-2012, 02:05 PM
Sam Thank you for your comments and I am not aggravated not at all. But I think you miss my point..:censored:. my point is this "why the gateway at all!!!" :payattention: In this case we are talking...
08-28-2012, 09:26 AM
After my last post I tried to maintain a positive attitude towards the JCI / York but I have to say that even after having job visits from a local Rep from York/JCI and Fieldserver the gateways still...
07-16-2012, 10:05 AM
The total product description is as follows
ProtoCessor FFP485 Camry
application software verison V6.06h (A)
protocol version 1
protocol revision 4
You are very correct in...
07-05-2012, 11:25 AM
After all of the negative reports that I have made on here concerning my problems with the S-Linc Modbus to MSTP Gateway I want to also report the Positive! We had a FieldServer and a JCI Rep come to...
06-29-2012, 01:17 PM
I received a phone call from JCI control department telling me that they want to visit to my site. They asked about local airport and hotel accommodations. They stated that they want to fix this...
06-18-2012, 11:31 AM
I have no idea but one thing is for sure, pure diligence and not allowing them to get away with it, is the only thing they respond to. The more you allow them to slide the the less they will do to...
06-18-2012, 09:46 AM
I finally got a response from my manufacture and their answer to my issue. I will let everyone be the judge of the outcome.
To fill everyone in I received new Gateways in the mail with no...
06-04-2012, 03:36 PM
In my case I listed all issues tested and prepared a detailed itemized list of problems. We did our part from testing with an oscilloscope to trying everything I could think of doing. My correct...
05-29-2012, 04:26 PM
As for me like I stated in the beginning If it was not for my customer I would have already done the modbus but my customer is wanting what he spec'ed so here we go! I do not know how it got to be...
05-29-2012, 01:07 PM
IMOHO They may or may not have even known of the issues at hand. I been in this trade for over 20years and been working in and on computers for even longer. The Idea of Alpha, Beta, Gama testing has...
05-29-2012, 11:59 AM
Not trying to judge. but it does not look good
At this point I am leaving the situation back in the hands of York/JCI
I have talked to many different people and I guess Fieldserver will build on...
05-24-2012, 01:45 PM
:oops:It is in essence a ProtoCessor FFP485 Camry and its made by FieldServer Technologies for York/JCI
05-23-2012, 01:41 PM
The reason I did not list company's, or name brands on this post
I have not done many posts on here and was a little concerned for the reputation of this forum. My mouth has gotten me into many...
05-23-2012, 10:30 AM
I too have seen poor Lon gateways but they are more uncommon than the RS485. Mainly because of the many different configurations and types of services provided ie. COV, Confirmed COV. Write on ...
05-22-2012, 04:26 PM
I have a soap box to climb on and something to say if it is deemed inappropriate I will submit myself for disciplinary action... but someone needs to say it and it might as well be me!
05-21-2012, 09:00 AM
I have gotten notified by JCI telling me that they do have a hardware issue with the ProtoCessor they found it on the ones I shipped back to them.
You going to press them to get a resolution....
05-18-2012, 11:48 AM
I did a FST Diagnostic capture under the requests from Field server this is what they told me after they got my Diagnostic logs
"I can see that the Bacnet client is requesting properties that do...
05-16-2012, 09:24 AM
New update this morning. I upgraded my site to 3.5.39 Sorry to say the Points are in the poll list but still are not updating.. I can still update the points just by looking at them in the virtual...
05-15-2012, 09:30 AM
[QUOTE=DCVoltZ;13214371]I did get the points to refresh but had to do many different steps which may or may not be the total fix to the issue. :gah:
Well I did not have to wait long for the...
05-14-2012, 10:27 AM
I did get the points to refresh but had to do many different steps which may or may not be the total fix to the issue. :gah:
1. Slowed down the MS/TP baud rate from 38.8k to 19.2k
2. Deleted and...
05-14-2012, 09:56 AM
@ kontrolphreak Most Gateways in my experience are very weak. In this case either their MSTP Transceiver supports COV or they do not.. According to their Bibbs and pics statements and to quote their...
05-14-2012, 09:41 AM
@ Berg2666 COV only makes it much worse was told by JCI and Fieldserver NO, NO, NO
05-11-2012, 04:29 PM
weather service is unrelaiable due to local network so no I do not use the weather service
05-11-2012, 03:58 PM
Running AX 3.5.34 Jace 6. Only two JCI rooftops isolated on their own separate MSTP port @38.4k all wiring practices observed. We did our homework and setup the port as instructed by JCI with no COV....
I found how to do this and thanks for the reply. I am still having issues. Distech posts the normal check your services and License SOP. It seems to me that if you use a binary point on their image...
Results 1 to 25 of 36