Type: Posts; User: The Punisher
Search: Search took 0.01 seconds.
05-25-2010, 07:25 PM
Thanx guys, will give it a couple of days and see. If not will call the Pros to come in and have a look.
05-25-2010, 07:13 PM
I just installed a new 3M Filteret filter where the return is. Is that the filter you speak of or is there another filter else where?
05-25-2010, 06:49 PM
I just had system installed last summer and we barely used it as it was end of summer and was not hot. Do you think I would need it serviced already?
05-25-2010, 05:59 PM
Humidity outside is 45% and inside the home is 54% where the tstat is located.
Unsure of the humidity level at start where the tstat is located, but in the master bedroom, i remember it being...
05-25-2010, 04:09 PM
Renovated the home last year, during this process, i insulated the walls of the house with R-13. Before that it was just double brick walls home. I added another 2x4 wall and added R13 insulation....
05-21-2010, 08:35 PM
I see thanx for explaining this to me. You guys rock :cheers:
05-21-2010, 08:59 AM
The Thermostat is a Venstar T1100RF.
Manual Link : http://venstar.com/Support/Manuals/T1100RFManualRev3.pdf
05-20-2010, 05:12 PM
Ok after some reading this is my understanding of what deadband is:
Say I have my setpoint at 22C and my deadband is 2C.
Means that the AC will only turn on at 24C and turn off at 20C ? Hope I...
05-20-2010, 03:44 PM
Thanx I have actually been searching here on the forum and read up on it and now understand it better. I have set it to 3 which I assume is 10min on and 10 min off.
However I am wondering, what...
05-20-2010, 02:51 PM
About to turn on A/C for the hot days ahead and setting up the thermostat for varying temps through out the day/night and I am seeing an option for "cycles per hour"
Now I am not exactly sure what...
03-19-2009, 06:36 PM
ahh ok I was afraid that this boiler would not be adequate for the steelrads.
Hopefully i get the ach soon and i can better evaluate the offers..
Thanx again, you guys rock.. Which i knew half...
03-19-2009, 05:55 PM
Is that a bad thing ?
03-19-2009, 05:51 PM
It says type L4006A , the rotary dial on it goes as high as 220.
Temp of machine remains at 120-130.
03-19-2009, 05:36 PM
Makes sense, the house has been at 21 the whole day and I only remember it being on this morning. Rads were cold when i went and turned it on now.
What does the honeywell thing do? It is set at...
03-19-2009, 05:22 PM
It still not shutting off, and temp is about 130. I attached some pics of what I have.. I remember once i set the home tstat at like 25 and the machine just kept on going and going...It never reached...
03-19-2009, 05:19 PM
Have no idea what those mean or even know where to check , My gas bill?
03-19-2009, 05:06 PM
correct the room tstat.. On the boiler there is a honeywell thing that can be adjusted, i never touched it, but it is set at 150.
I am watching the actual needle on the other stat, it has...
03-19-2009, 05:00 PM
So my stat was at 21 and I set it to 26. Boiler turned on, and now I am waiting. So I should wait until it hits 26 in the house? and then check boiler temp? Right now it is around 110-120
03-19-2009, 04:47 PM
ahh ok so i gotta look at the thermostat on the boiler and see how hot it gets..
Inspector guy just got back to me, says he still has to do the calculations in order to get ACH. Says he will try...
03-19-2009, 04:27 PM
not sure i understand what you want me to do?
03-19-2009, 04:23 PM
Yup just called the company, they said the ACH rate will be in my report which i should get in 2 weeks. I explained that I needed that rate sooner, so they gave me the inspectors number, I called and...
03-19-2009, 04:10 PM
They never did tell me the ACH, they did the pressure test on the house, and all he said was that it was pretty sealed up, mentioned that I should weatherstrip my basement door but no other real...
03-19-2009, 03:52 PM
after having dropped the infiltration to .85 value I now get about 36814 heat loss.
Still find it high. But if it is correct does that mean that my rads BTU/h output needs to match that or be...
03-19-2009, 10:25 AM
OK that is what I figured and therefore did not add those walls. I have the winter infiltration set to 1.05 which is what the software recommended.
The Main floor I have listed as above...
03-19-2009, 10:01 AM
Nope, didn't add in duct work. The software says 31000 is being lost through my walls. I am in a semi detached home with double brick walls and lathe/plaster on the inside.. Never found it to loose...
Results 1 to 25 of 49