Type: Posts; User: sol
Stulz is the way to go.
Units are efficient and reliable.
if it's a unit with ICOM display password is 149
The no fllow message is normal for the way the new E2 controller is set up at the factory and goes away as soon as the chilled water unit sees a change in temp of the EWT and LWT.
makita the only way to go
Call Crawford Mechanical Services in Phoenix. They will be able to help you.They have been really helpful to me
Thanks for the comments , I think i wont be getting the fluke even though
I have a 902 which I love!
I'm looking to buy a digital psychrometer and I basically need it for wet bulb and dry bulb and relative humidity.I also do not want to spend more then $200. These are some of the psychrometers I'm...
Thanks for the info, i've got a controller and a psc motor on the way.
I have a mini split that keeps burning out the condensor fan motors. It seems to be wired so that the compressor runs when calling for cooling and the condensor fan will cycle on and off only when...
I found out why the lines were buried ! It was to quieten the lines . That's what the home owner told me.
Work in Phoenix and looking for hvac work , going to school in mornings
I serviced a 5 ton split unit that was about 10 years old. The suction line and liquid line out of the house to the condensor runs into the ground and then using three 90 degree fittingsthey lines...