Type: Posts; User: jay688
scratched my head on it a couple of hours before i figured it out myself
this guy should of installed,,his airhandler and ducts in the a frame attic.
or airhandler in interior closet,,up to attic and ducted to each room.
a/c should be on the side of the house where you...
johnson controls is the way to go if you can afford it,,
$600.00 here,,,but the twinning features in most of the white rodgers boards
will work as long as they are wired from the same bus of the...
pull the cover off the panel and make sure your coming off the same buss or leg
that will remedy the problem:D
i had the same problem,,you have to make sure the 115 volt line feeding
the furnace is pulled off the same leg or side of the power panel to the house or space,,( that means two seperate feeds off...
do the customer a favor,,and call the health department.
or better yet just loosen some gas fittings and give him a cigarette
as your leaving he-he
is that metal?? it looks like that old pasteboard they used to use in old tv's to isolate the fylback transformers from screwin up the tuners:D
looks like 14 seer units,,so if im not mistaken,,he hung his condensor fans on the electrical service/ service side of the unit-which means theres still a metal partition for the board and contactor...
thanks everyone who replied to my post,,
i will return later this week to try all the suggestions:D
i know i'll probably get bashed for this but..
i have a condensate issue im sure one of you guys have come across,,
so here it goes,,
i have four identicle yorks on a rooftop 3 of them operate...
the leasee wants to rehab these units,, i told him he basically lost them three years ago.
however im always up for a good chalenge,, i'll post the pics as the work progresses.
you get the grand prize,,it is or they are temperature controls inc. units
looks like some sort of heath kit commercial gas pack units made here in atlanta ga.
or should i say the...
i've been to the mcquay website,, and cant find that particular chassis,,cant find them in all aluminum either,, still looking
thats worth tryin,,, is the pope still in the states,,or did he leave allready..
hey mike lcs,,
the stats are 24v and the hx is a clamshell design-
its a weird one,,but ive seen one posted here before,,, just cant seem to locate it one the search
so i get the call that the ductwork in the back room has an odor to it when ever the heat or air comes on? take a look at this!!
right blower door off,,both front covers off-both units standing...
hey al o
i think thats what it is too,,from the old washed out tag,,
couldnt find it on google tho,,, still checking
lets see if this can jar anyones memory??
control panel // somewhat modified
washed out id tag
i will post the layout of the componets and a washed out id tag
i'll do just that mannyleonard,,
and then i comin to work for you he-he
your not steppin out of bounds with me and i dont mind you asking at all,,,
i've been a member since this site was at its infancy,,
also i own hvac calc,,and consider myself a...
amen to that mr antley,,
i'll check mcquays site and see if i can find a chassis thats similar,,
and thanks for your help,,this guy would replace them all-but his old hacker,,did this to all his...
i figured you would let me have it good,, for even reactivating these old dogs,,he-he.
but the guy is gonna replace them before we hit another heat season.
i like how they just bent...
yea i told my client he lost those units about three years ago,,but he just rents the space,,his old guy was an illegal and a hack,,and really screwed him good.
all his store run about 45% capacity...
got a call on a twinned goodman down,,couldnt belive what i saw!!