Type: Posts; User: Milk man
You are walking a fine line,but I do not think you crossed it. I support everything you posted.
Verify the condensate tubing is connected like the manual shows. Pay attention to the section about the trap being not on the same side as the exhaust pipe.
I'm talking about the tubes from the...
Is the condensate drain on the same side as the exhaust pipe?
Outdoor coil will frost easier during the heat cycle if it is undercharged.
I like the W. R. Eazy Reader stats. No need to an outdoor sensor.
I could be the placement of the sensor. Is it in the sunlight or mounted under a drier vent?
A well trained medical professional killed my Mom.
What is the model and serial number of your furnace?
The veterans at the Kennedy Center Honors were not saluting Obama. Why would he deserve a salute? What has he ever done to earn one? Can't wait for the day when he is out of office so no one in...
Is that a Goodman GMP? If it is the heat exchanger's rings could be popped. Really need to pull the blower and look for the rings and do a heat exchanger inspection.
It may be possible that the stat is single stage and the furnace is set up for two stage. This would run the furnace in low capacity and maybe not keeping the house as warm as you want it.
Your condensat trap needs to be cleaned. Your heat exchanger needs to be inspected. Very important if you are on propane.
Yea, talk to wife. Knew that was coming from a mile away.
All hail the king.
Suck it up and move along. Life isn't fair. I know this first hand and I'm still fighting some job related bitterness myself.
Best advice is just move along and forget about it.
Ever notice how many friends you have. I never knew how blessed I was.
It is a huge pisser to me. Always install unions. Just makes a good install. How many pms have been done and the claim made the condensate was checked with an unserviceable drain.
My thought also. Also piston in backwards or missing
You can look it up in a handbook. Copeland can be downloaded. Others are available also.
I'm with bad blower bearings, CCH, and dirty coil. Also overcharge.
Bad neutral to the house sends 115V appliances searching for a neutral through 230V appliances leading to greatly increased (or decreased) voltage on a single leg through the capacitor. W/ no...
If it was working this morning, then this problem could not have happened 8 months ago.
After going back and replacing capacitors I replace recently I've started using two, actually three, in some cases. For instance, if an 80 MFD needs to be replaced I might use two 40 MFD and a 5 for...
It's happened to me. I always ask the office for their number. They never seem to get it. If they would I'd call and ask where they worked so I could complain about them.
Depends. You can recouperate the cost of a new system with energy savings.