Type: Posts; User: IRBH
Search took 0.01 seconds.
Go reset your breaker(or fuse)...one side tripped, feeds to other leg via cch etc.
Does this system use clutch-cycling?
If so...is the compressor cycling off?
(Sorry, but I don't plan on using much of my alloted time learning Hyundai technology.)
Your readings of 0/150 are ok.
As far as holding at 4.5A, that would be at full load & highest allowable ambient & min voltage.
Don't set it to -5f with 10 diff.
It's taking 3 full hours...
Get a spun-copper filter/drier c/w access valve.
Guessing about 12 bux, may be almost give away in good old US of A!
Evacuate from both valves.
Envision... you'll have to donate that freezer to the Smithsonion.
45 years on that old AT43 and still going!
With a perforated line & zero freon, that freezer would have been inhaling &...
Good description, 1CanHas, but errors in second-last paragraph may confuse some.
Get familiar with SH and SC for recharging.
If you can, buy some Sman3 digital gauges & do SH SC WB temp for target SH on every job that you do.
Try to determine the reason for any out...
All the more to you for finding it.
Way to go!
Sorry for screaming, Redman1126 but it was so obvious.
But that was EXACTLY my point.
Reading comprehension skill
Then explain why the pickup is only submerged 1/2 inch, and the return goes to the bottom of the holding tank?
Ok so the pump is proper rotation.
But could the suction/discharge hoses have gotten reversed?
Magoo, we've run into the same condition.
Do your AC's have economizers?
I remember Toronto cooled off from that lake Ont breeze quite nicely.
If so, suggest you disable them. It's not...
Very good to hear, Kefah.
In canada we're hearing terrible atrocities are going on over there.
We're sending plane loads of arms etc to the Kurds.
Food, shelters & other help would also be...
Called to a new building's RTU installation.
Of 5 Lennox Prodigy units... 3 not working.
Two LPS not connected.
One flat, leak at bottom of evaporator.
Tagged for warrenty...
I notice there's no reply from Kefah in any of his threads.
As he's from Iraq I sure hope that he is not having to flee in front of those SOB nut-job radicals. Hope Kefah is nowhere near the...
You should do away with the condenser fan completely.
Perhaps drag the dog house next to the unit.
On really hot days call the dog's name a few times so he wags his tail.
PHM, you'll break...
And in between is a standing puddle of current?
Of course you meant v.
Used to be called "recirculate", ie a closed loop.
Cabin air only rerun thru evap.
Also the setting for passing cars on dust-choked back roads.
Kefah, measure the voltage developed across the capacitor.
Only excess v and overly hi temp kills run capacitors.
Bad batch of capacitors?
Try two double mfd capacitors wired in series, ...
[QUOTE]... I took the readings to ground and measured across them. 120 to ground, less than 1 across.[ /QUOTE]
Key sentence here.
Bet if you grnded the blower neutral it would run.
I wasn't joking, but good answer!
I was getting to ask you if it has a board of any kind.
Also, all these v readings... is that to grnd?
You sure your neutral's intact?
A few questions:
What ohms reading were you expecting on the secondary?
Since you got a new xmer, did you compare resistance readings?
What's a 70% efficiency air handler?
I don't think it works that way.