Type: Posts; User: Joelfu27
Search: Search took 0.01 seconds.
It is better to remain silent and look a fool than to open your mouth and remove all doubt.
It is probably a cooling tower.
Just like new used maybe 10 times. I'm lookintg for 125 for it,. They go for 225 band new.
Call ME AT 954-665-4678
MY NAME IS...
04-06-2011, 04:58 PM
The water lines in the heat pump are 1/2". Now the loop lines to the unit are 3/4". The lines reduce to 1/2" after the shutoffs. Now we have had problems with some of our ice machines that use 404a...
04-06-2011, 03:49 PM
water inlet temp: 72F outlet: 148F
low: 135psi High 525psi
suction line temp 71.7f
water inlet temp: 72f outlet 29.8f
unit cuts out before a reading can be...
04-06-2011, 09:23 AM
I work at a hotel that uses mostly R22 Macquay Heat pumps in the rooms and any other space. The hotel is 8 years old and a few of the compressors have failed. The owner had the first 1/2 ton room...
03-03-2011, 01:26 PM
I am working on an ice machine and need to charge a few ounces of 404a to see if my low pressure problem is from a low charge or if the problem is the txv starving the compressor.
Do I need to...
03-03-2011, 01:12 PM
Thanks, I may have someone bringing me a drag line socket, if he can find it.
I have a replacement sight glass and gaskets coming in today too.
Thanks for the tip
03-03-2011, 11:55 AM
Does anyone know an easy way to remove the sight glass from a compressor?
I know there are sight glass removal socket pieces, but I'm trying to get this done today and without damaging the sight...
Results 1 to 10 of 10