Type: Posts; User: qtip
Sounds to me like an equipment issue not a controls issue. If your not making airflow there is not enough fan to produce it or the drive is set up wrong. .85 is pretty low static, Air Balance report?
Which version is the SC?
HUI or Configuration access?
Clear the cache in your web browser and try Google Chrome.
if you have an auth code shold not be an issue
No problem with TU. Many problems with Tridium and the patches do not work either.
I can't stand Summit but your question is to vauge to answer.
Replace the valve stem spring and packing...known issue
That explains it!
BTMX or BTMW?
Wait till your 46! :cheers:
:cheers: Well put.. Do I get the chocolates
Global warming?!? Kind of skeptical in my opinion. This planet has been around for an amount of time we cannot comprehend. The Siberian Traps erupted for a million years and produced more global...
Get used to stress and very little sleep, and the phone ringing all the time!
The patch did not work for me on my last job
I don't get it! :Faint:Who would use one of those to fake a sensor out? :Faint:
Depends on which control board is installed in the drive. There is a 24v or 120v version. Review the manual that comes with the drive and wire the source power from the terminal block and return it...
Is it licensed?
Thanks the Linear at .1 did the job of moving the decimal and Facets are set to Deg C but how can I get the output to Deg F?
This is a Vykon Jace....No rebranded JCI stuff
I have a boiler that is Modbus and they are sending temperature data out in deg C but with the decimal point in the wrong place, 580.1. I need to devide the number by 10 to get the correct data. Is...
Make that two tickets