Type: Posts; User: cold don
lived sw fla. 15 years outside temp., has never reach 100*!! might feel like.
recovered freon cut bypass copper solder both ends ,"heatpump ahu"evacuated recharge suction pressure good, thank for input
if you read my first message the unit was off smoke detector.unit been running this way,most likely from start up and person walk away.
didn't take superheat had to go to another job ,know i be back this monday
txv,5 month old system,os temp 95 comp.amps 27 cond. fan ok evap.ok
billva gess your not a pro/i've been doing this 15 year,can always learn something.thinking i have to look for restriction
you need to remove coil ,chemicaly clean.then check air flowand split,have fun replacing duct work
ahu trane m#twe060c15fdo s#44355y52v 75' ahu 20'higher then cond. pipes 1/2'liquid 11/8 suction unit down smoke detector started unit 62/320psi found ahu is heatpump/but condensor not,unit is...
sales man should of asked if you were going to help his tech then double yor cost
yes 3ton c/u,3.5ahu all 1st floor condo's,capacitor checked and installed hard start.evap fan low speed 3.2 amps,replaced txv to eliminate.when unit cycles at temp.or shut off manually is when...
compressor gose off overload.after comp.replacement openwinding.c/u m#10acc-036-230-02/s#5805b12391 ahu m#cb28uho4223001/s#5805b12977 condo 1st floor,line set 3/8,7/8 under ground.on start up ran 5...
need more info. Are you resetting brakeror oil safty?check amps at unit and braker panel tightenall wires,maybe weak braker
going to replace system box size 9'5"x7'2"x8'high need box -5* best freon to use? evap.size c/u size
thats what i thought customer didn't spend 3 more bills for condensing unit now paying the price.will recheck 8/2/05
10'x8'walk in freezer compr.grounded r-22/txv404a.installed new compr.404a & new txv.started unit suction pressure wouldn't go above 11psi/replace txv same thing.change txv cartrage to #3. ran two...