Type: Posts; User: rdjr64
Interesting experiment, all us techs are glad you did it on yourself and not a customer.
Can't find help like that around here.
It's a Goodman!!
Not knowing the law is no excuse. Read up! It can save you hassels and money.
Your lucky, even if she let you clean it the compressor is probably either sick, dying, or doa. Imagine trying to tell the customer more bad news after cleaning?
Not upside down, both the air handlers are installed correctly but one problem, you can not access the blowers.
Looks like benncool knows his airhandlers.
I think the home owners need an edjumacation.
These units are installed on opposite sides of a stage. Were blue prints involved?
[Edited by Boss on 12-29-2003 at 10:04 AM]
So if you don't have a/c then you ask for a Big A-- Fan.
So if you don't have a/c then you ask for a Big Ass Fan.
These five blonde ladies were in the office jumping up and down yelling "fifty-one, fifty-one, fifty-one" when the boss walks in and asked, What is the big deal about fifty-one?
One of the ladies...
Sounds to me like the homeowner was trying to save money converting a straight electric a\h and straight cooling condenser to heat pump without replacing the entire system. May not be previous...
Can I, Can I, please I want to put a drain line in, just one more?
[Edited by rdjr64 on 03-20-2003 at 11:16 PM]
In Wacko Texas? Would the next Baylor braniack please stand up?
It's a new frozen chinese secret.
I wish I would have taken a picture. But we never went back. An AHS job. Of course denied.
Adding: May the owners wanted a two stage systems. ha
I can't believe they didn't disconnect the drain line from the old unit. What were they thinking?
I would call the contractor and disuss it with them. If they refuse to bring it up to code, then I would contact the Licensing and Regulation department. THIS is a disgrace to the HONEST contractors.
There is a Good Man and a Bad Man. The Bad Man runs the Good Man buisiness.
I can't remember the brand name of the Plenum/coil combo but some of you probably have seen them. Checking a unit, it was frozen. Shut off condenser and returned the next day.
Re-started system and...