Type: Posts; User: HINDUSTANI
Search: Search took 0.01 seconds.
07-20-2012, 06:57 PM
I need your technical suggestions to rectify the below problem, I would like to brief here shortly.
When we commissioned the RTHD chiller with solid state starter ( Chaina make) chiller it was...
All our systems are closed loop operation for comfort cooling.
Most of the failures are during the project times. (untill the condition not matching the required Trane commissioning specifications,...
Yes your right. but a small change - regarding the No flow (the flow switch is in line). my findings is inadequate flow.
All the damages (I am not able to openly disclose the number of chillers)...
sorry. pleae read the 12.30 posted statement.
Pump operation through the CH-530 is very simple. Timer controlled ON/OFF operation with the help of a relay and in addition when ever the temperature fall at or below the freeze...
The operation sequence is - 1. Once the chiller in start command (whether in Local or in Remote Mode),
2. After few seconds, the motorized valve opens.
Totally Factory wired.
The Pumps are not rooted through the CH-530. Why because - our climatic condition is always hot. My understanding is - this pump operation through the CH-530 is Exclusively...
Regarding the power - With in 60 Seconds power resumes with the DG.
Regarding the Barrel heaters - for 44 degree F set point operation, it takes more time to raise the temperature of the Evaporator...
Model number required.
Results 1 to 10 of 12