Type: Posts; User: richvacr
A wise man's heart is at his right hand; but a fool's heart at his left. Ecc. 10:2 KJV
I asked a few weeks ago and problem has not recurred
Last thing a few days ago is that they are getting financing to pay bills - so we were told
Does anyone have experience dealing with MTL Cool out of Quebec Canada?
Been trying to collect on 3 jobs performed in the states but nothing
Accounts payable is out of the office and non...
Funky looking but t off the same source
As for where inside the wall i do not know not in ceiling so either from 3 compartment sink or hand sink
If HGV is sticking it is not when I am watching it
Dip switches were set to factory default
Machine resets - thermistor if it is the problem is intermittently bad
could be but why only the top not the bottom
I would think faulty thermistor would be more consistent - at least one out of three cycles
but i told them i will price a thermistor since it is the cheapest fix
I have a KM1300 SRH stacked units with the top unit every couple days going off on high temperature safety (one beep)
When I reset and run it everything is close to normal (freeze time is a bit...
What is needed is a either a push rod or if the door is locked an internal way of forcing it open
I know when i go into a beer cooler especially that has a padlock I take the padlock with me...
I have been tempted to get digital gauges - Testo's I lean towards
But I wonder how much a difference it could make
I'd say my sense of touch & hearing play a large roll (well sight to as a giving...
Yes I agree but what are people thinking when they mount it in the supply
Thermostat sensor like a A19 mounted so the supply air effects its operation.
I have come across this a few times and I don't like it. For a while I thought someone did not know the direction of...
Does anyone here have info to learn more about solar hvac applications. I looked Lennox thing.
Is there anything else out there?
I have been using 15% for sometime but the price is getting crazy. Are people switching to cheaper stuff or paying the price.
Wish I bought a box when it was around $50 then I could sell it on...
Having serious problems with a polaris 130 installed since 2003 (w/o problems) at 5000' above sea level.. Polaris when asked said nothing about elevation.
Not the first on the scene the others...
My gripe is the amount of paperwork and their dysfunctional website
I can not input the proper local tax rate (fm does not have a cert) in the quote but can in the invoice
Why do I have to re-enter...
it you have the change the txv because it is malfunctioning possibly from debris changing the lld would be a good thing.
damm i must be slow not sure if it could change it out with presssure...
7 rtu in an hour by yourself? it would take me about that long with gear to walk between units
maybe you use the makita impact not just for screws
Thanks that answered a few questions.
Now it looks like there is a fault with the board's compressor off timer because I had it running for a while before I took the covers off and found it to...
Today I came upon a Carrier 38tdb060310 with a problem with the condensate pump - replaced that but
Back up a minute. The unit is running off a single stage tstat (enough wires to convert to 2...
As far as i can tell water flow is good the 3/8 tubing from the chill pot to the resevoir apears to be at max flow
Temp controller just a mech tstat remote bulb in resevoir and a freezestat in...
filter need to be changed - none on hand but water flow is good
to me dirty filters would lead to low suction pressure, chiller cycling on freezestat
Forgot another thing did a compressor efficency test packed it and held 10" hg vacuum for 10 mins.