Type: Posts; User: pecmsg
I thought you don't change one but both on tandem units
Contact Mitisubishi. I'm sure if the problem is on there end they will want to know about it.
No one can answer that. How do you know you only have 2oz of R-12?
Change drier and go with Hot Shot
Is there really that much out there designed for R-22 and in warranty?
You can’t find the leak.
Auto feed valve closed due to over pressure.
200*f way to high.
Sir you have a Bomb in your house please, please, please call for service.
No excuses your life and...
Copper Only where Heat Tape is used.
I agree with CJ many Combo WI drains with no traps and no problems.
it wasen't the refrigerant!
If you can live with the oil that will be carried over.............
and dont forget no cool gas coming back for the windings it probably wont survive long.
they will start the problem is what damage was caused. This is new equ, the oil has been baked what are you going to do in 30 60 90 days or next year if something fails.
To me its not worth it,...
I show 2 contractors on our locator map:
Firebird Air Conditioning & Heating
PO Box 71125
Phoenix, AZ 85050
Wolff Mechanical AC, Heat & Solar
Dear Hot Tub Owners
Due to damage caused by phase rotation during recent electrical upgrades the compressors in your HVAC system must be changed. This work is not covered under Warranty.Your cost...
Mini splits have a place, primary cooling of a server room is not one of them.
Server rooms require constant control of temperature & humidity. Minis cannot do this.
There is a good reason...
Anyone can do it!
Also install small electric baseboard as back up
R-22 Starting Point
Fine tune the CO for exact temperature
What controls the compressor, pressure or temperature?
Unless you like to spend $ of fuel put the snow melt on Solar. 1 or 2 days after the storm your driveway is clear.
Do a search on ice merchandisers. There's a ton of options. I still like K D 1" cubes, hoshizaki makes the same ones
Plumbers use Lead Free 95/5
Stay Brite 8 is a low temperature (750 *f) Silver bearing solder
R-717 or R-744
Temporary solution but will help
Boilers still not big enough during usage.
I’d add an oil fired water heater