Type: Posts; User: tinknocker service tech
Search: Search took 0.08 seconds.
1 year expect some where between 10 n 15 per hour if there is work
things are slow here and may take time for it to pick up
12-24-2012, 09:04 AM
20 gallons a day and it isnt water logged you have a leak some where look for it before you damage the boiler
10-14-2012, 02:18 PM
just saw the vidio. Looks like the typical nc system. Looks like you may have a damper zone system from the control on the furnace.
you would IMHO do better and save more by ripping it all out and...
yes it does
the termintions look a little close to the corner
most units want up to 8 ft from a corner or side wall
was a permit pulled and was it inspected??
09-30-2012, 05:53 PM
there is some info missing
test resolts are important here to answer properly
if it is warm out then yes drat could be low
what were his reading after the unit was running for a while like 15...
08-26-2012, 08:54 PM
have to agree with Been on this one
your leak should not be that hard to find and dye is a waist of time
08-26-2012, 08:19 PM
you have said you have no intentions of useing this guy and stated he was an idiot
he from what i have read did the load calc with a few minor mistakes witch leads me to think he did more for you...
07-22-2012, 09:37 PM
have the coil cleaned or at least the typre you sray on from a can and let it run off with the condensate
sounds like it may be pulatants with an oil resadue
07-15-2012, 09:39 PM
how is it vented? May be tripping on presure switch
flame senser may need to be cleaned often if the gas isnt burning properly
If it has the wrpilot sensor with the 45sec delay the secondary...
water flo is important
if the new pump is 600 gph you may need to up size the intake piping to it and upsize the outlet piping
you realy need to find the exact water flo you need to run the unit...
07-09-2012, 11:29 PM
with the 20i unit you need the trane zone panel and proper stats for that panel
any other zone panel will not work well and or stage the unit properly
trane also to the best of my knowlege...
i have done many unit on log beach island that went under decks and walkways
some only had 12ins of clearance
i would put a full size square elbow on the top of then to shoot the discharge air out...
have your friend juice it up for another six weeks and maybe you will be able to find a job and be able to replace the unit before to long
if nothing else it may get you through the rest of the...
what doc said
capacitors dont always look bad they always need to be tested to be sure they have the proper rating
07-08-2012, 10:01 PM
back in the day it was not uncomon to find a unit on a roof or in sun on a 100 degree day to run at 350 or so
check it when it cools dow if it ever does
fan relay come to mind
time for the techs to do thier job and fix it
mr bill i heard they are now useing horses
07-08-2012, 08:59 PM
not sure any of us can be of help. We are limited on just how much advice we can give
tell us what is happening and decribe the best you can
if the coil is clean and the fan blade isnt blowing hot air through the top of the condenser coil raising your head pressure
you may want to check your lineset for a posible kink and someone is...
very informative tread
i was taught in a few class that you bring it close as possible with liquid and you can fine tune the sh n sc as a gass
aside from the fact the helper was in the wrong and...
07-07-2012, 06:21 PM
come on give the guy a break<<< he is trying to learn as we were at some time
100 years ago when i was first starting beer can cold was the way it was taught. as time went on you learn the right...
found years ago in a weak market more isnt better
charge what you charge and hold level and the customers will still be with you when the market is better
a good tech is worth his wieght in gold...
07-07-2012, 10:57 AM
didnt see the size of the unit so spoke to soon on cfm
i do tend to feel there is an airflo issue
07-07-2012, 10:41 AM
anytime you go on a call you collect diagostic repair or not
this means you go through the entire system and check it out if approved you do the repair and check it over again to be sure you havent...
07-07-2012, 10:18 AM
very posibal they took out the one and forgot to install the one in the bag and there is no piston
pump it back and check
Results 1 to 25 of 500