Type: Posts; User: shaka
Search took 0.02 seconds.
I usually convert it to txv and im done..
I'm in Texas
I want to go to Florida
Sent me a ticket.Lol
Agree with rundawg..
Ohm out DT.
Dirty coil is probably your problem.
If you have a static pressures close to .5 across that coil, air flow start to be unstable.
Condensate can actually fly off the coil at those pressures.
How are you converting it to piston?
do you have a fitting to connect to male thread on the coil?
Evap coil on furnace
Evap coil is leaking and I need to replace but need to make sure it's an approved match
if you have the extra wires like I ask that means your motor is after market.
I you changed it and installed the same horse power, that motor will mess up.
Like timjimbob said the oem will...
Is that mean according to watt to speed ratio your fan is actually running at 1150 at high speed?
Do you remember if the motor had the extra wires to change rotation?
Do you have pictures
You can send to my email on my profile thanks
Wow 2.5 amps and cools my garage
Do you have model number.
How much was it
I do feel hvac contractor should be the one installing the water heater.
we can handle the the install and the equipment in case it goes down.
I guess if the plumber install it, he would...
If the water heater was indoor and it's winter, that might get the house too cold.
I guess you could run just the auxiliary heat in the winter.
So the new unit uses 134a or 410?
How old is your water heater?
Do you like it?
Do they call a plumber? I don't think so
I was just looking at a heat pump water heater
Any time now we will be working on the water heater too.
I was thinking of installing one for my...
What's your pressures.? SH,SC
I don't see how you have a restriction with no superheat.
We need more info
Too bad you can't pressurize the condenser then
Throw it in a swimming pool :grin2:
You don't need to remove the mineral oil.
I have a walk in cooler with approx 50/50 of MO and Poly
Been running for over 5 years
Why do feel you have to flush when you convert to 410?
Yup they got into your pocket.
I have never used any RX11
Not even on burn out.
I think I have 3 diff one
But I don't use any of them. Lol
Ohh forgot to tell you if the resistance value way off the specs
Compressor is bad, you need to replace it.
Ignore my last post where I tell you to calculate the back emf..
Also get model number of the compressor,
Check the original specs on compressor
Compare winding resistance,
May have weak winding causing potential relay not to drop out right away. ( cabbboomm)
What's the voltage across run cap.?
Run usually goes out by high voltage issues,( cheap cap)
Start cap usually goes out due to short cycling,
So check make sure it's not short cycling.