Type: Posts; User: iceman134a
Search took 0.00 seconds.
I have not heard about any switching to metal gaskets,
let us know what Pueblo said.
We used to use o-rings w/loc-tite-515
Eagle should have bullitins & part numbers for all,
slide valve, terminal plate o-rings, etc.
There may also be an unloader svc bullitin.
I had a feeling that you were the German 8er
It was really good seeing you recently @ Hotskins
Min. return temp. for Lochinvar boilers is about 140*F.
in otder to prevent excessive condensation @ boiler tubes
The advise you have been given is all good.
Also be sure to do a high pressure leak test of the entire chiller. These machines are known for leaks.
Especially check the compressor motor terminal...