Type: Posts; User: temp55
what you need is to do a load calculation. dont go by square footage.
I'm looking for federal money in installing 3 VFD drives. Can any one help.
this is the responce i was looking for, and the job is basicaly the one i was looking for because i like the money but how do i locate a job like this. if you know, my e-mail is firstname.lastname@example.org
I,m looking to work in Iraq for Halliburton, if you have worked there, please post, i would like to know the working conditions there and pay.
Is it worth it
some older carrior RTU"s have an internal trap that clogs up, to repair you need to remove the pannel on the side of drain and remove internal trap then intall the external trap and clean the pan.
I have noticed when you get a no cominication code on the board all i have done is remove and replace all the connectors on the board and your up and running.
I have seen this before, your problem is your lines and there is nothing you can do about it unless you change them, TXV will help and also watch your temp at the suction line, mid 50's is good but...
I have found that if you disconnect and reconnect all leads on the board the alarm will go away.