Type: Posts; User: cody350
Search took 0.02 seconds.
Lennox icomfort wifi thermostat
Lennox cabinet and merv 16 filter
Lennox bypass humidifier
new electrical to panel
new pvc (used to be 3")
new return from transition down
metal looks good.
tell your boss dave the next time i see him i will proclaim him KING OF ALL AIRE-FLO! haha
the board is mounted to an interior wall. there were no plans to insulate. i agree, it's a lot of copper but you have to realize too that this is a really old building downtown and there is no...
the diamond plate i think was actually aluminum, we mounted a 4x8 sheet of the plate to plywood and it's mounted and anchored to the wall but with a 1/2" gap so as to avoid moisture issues
that wasn't what we were going for.... but sure!
ironically, i looked up the instructions online for the boiler buddy (after my other boiler post) and found nothing noted about check...
I know many of you busted my hump about not painting the board on this install....
The pics below are of a new...
too bad "Dirty Jobs" is no longer on the air....
I'm not sure there's enough latex gloves on earth to get me to work on that stuff!
ok, I might work on it after you got done cleaning it cause...
Interesting, I'll have to look that up. Like Charles had mentioned.... it should be taken care of at the zone valves.
I actually saw a drain like that on another boiler and thought it was a...
The heat is included in the rent, this building is really old and there is really no easy way to split up heating. As for the paint, I'll be posting more boiler pics in the future and...
I can't take credit for any of the piping or much else....
I'm just the wiring and start up monkey!
7- Callefi "pop top" zone valves
2- Honeywell Wireless Pro6000 tstats
what did the home owner use to heat water before?
wouldn't a conventional forced air gas furnace and power vent water heater be cheaper?
i never understood hearing some of you guys talking...
I just spit all over my screen laughing
is that furnace powered with an extension cord?
that can't be right
just out curiousity
for a complete change-out, indirect and repipe like that with setup of burner.... how much time does that take? how many guys/hours?
i'd certainly pay for that kind of work
on the last pic i notice the expansion tank on the domestic is upside down.... i was always taught that's a big no no
either way, ridiculously clean for...
i have NEVER seen one of them thingers
why exactly were they used? did they not have heat otherwise in the bathroom?
i'm assuming it's a wall heater by the title of the photo
they left the evap coils!
i get SO pissed when i walk onto a job like that!
don't get your panties in a bunch man.... haha
my unfiltered thoughts certainly got the better of me and it obviously rubbed you the wrong way.
what it boils down to is this...
did you check...
i wish there was a "wall of ridiculous"
i hate to be the one guy that looks at this and thinks it's stupid
talk about restriction....
did you check pressure drops across all these filters...
looks like someone worked for airtron haha
ps, RNC is residential new construction
north prairie? you bet!
as for the purple primer, it's actually a mark i made with a sharpie to line up my 45's. just makes my life a little easier, the other marks were cleaned off better with...
it is a single stage stat, that i just replaced when i did the a/c. there is enough wires to run a two stage stat but i'll wait for this stat to die before i go to two stage
it's a merv 10 filter...
i know, i used it haha
i answered in previous posts, yes all the dip switches are set properly, i'm a service guy
and the return drop is 8x25, the trunk line i think is 8x14 or so