Type: Posts; User: Gunslinger
5 gallon bucket
Shut it off, use your emergency heat function. See if there is ice built up on the fan. You do not want any ice on the fan blades. You're best off calling a service tech.
Spectronics dye is oil.
you'll need to give that info, yes. Also, if you're saying they used panning for returns, yuck!! If I were to be sent to check this job, I'd measure the statics and delivered flow to each room.
when doing a manual D, they hopefully determined each room's needed CFM was the larger of the result. for instance, if one room had a larger required #cfm for cooling and another room required a...
Are there returns in each bedroom?
Just for business use and emails, downloading manuals for troubleshooting...what is the recommended amount od bandwidth? is 3 gig enough per month? What are you all paying?
I aalso question why zone. When the ones close down, it is my understanding that the by-pass opens sending ctempered air back to the return. Thjis doesn't seem to save money or increase efficiency...
link does not work
It may be moisture in the oil. Try heating the compressor with a heat gun and rapping it with a rubber mallet. As previously stated, over night evacuation may be needed.
model year and roof type would help to answer your question.
I would like to know metering type, indoor wet bulb, air flow. Give all the parameters
I have purchased Johnsons R134a from Sams Club mny times and have never had a problem. The fitting on the drum is an acme type but there is a plastic adaptor in the box. If things have changed...
what are the model numbers on the compressor?
1/4 inch and I braze it with 45%
I also make mine from old hoses.
They may be on the way to Comfortech.
Dropping 6* in 40 minutes during the heat of the day tells me you're over sized.
what did your load calc say? They did do a load calc, right?
Call Traulsen. There are a few things to check. The relay in the control box can be intermittently sticking on so the bx runs continuously. The sensor that monitor cold box air that is held in the...
same problem here. I have to scroll to the top and hit the back button twice.
I would not purchase hoses with quick seal connectors on them. The connectors fail way before the hoses do. Purchase sealing connectors separately. Why do you need a 10cfm vacuum pump? A 5 or 6 cfm...
I think they may have used a summer design a little too high. They used 99*. For San Antonio I think 96* is more in line.